ceiling fans
century fb1056te condenser fan motor1 2 hp1075 rpm60hz
condenser fan motormotor design permanent split capacitormotor enclosure design totally enclosed air over1 2 hprpm range 1001 1100nameplate rpm 1075voltage 208 230 46048 y framenumber of speeds 1overall length 13 3 4 in.shaft length 5 in.shaft orientation upfeatures reversible auto protector open lead endmotor shaft rotation cw ccwfull load amps 2.4 2.4 1.2 cradle base motor mounting typethermal protection autoinsulation class bservice factor 1.0 br b features b ul li body dia . in . 5 5 8 li li features reversible auto protector open lead end li li full load amps 2.4 2.4 1.2 li li hp 1 2 li li item condenser fan motor li li length less shaft in . 8 3 4 li li nameplate rpm 1075 li li number of speeds 1 li li phase 1 li li ring to ring center in . 8 5 16 li li shaft dia . in . 1 2 li li shaft length in . 5 li li stud pattern in . 3 5 8 x 3 5 8 li li stud size in . 8 32 x 1 1 2 li li thermal protection auto li li ambient c 40 li li bearings double shielded ball li li capacitor required included li li duty continuous air over li li enclosure totally enclosed air over li li hz 60 li li insulation class b li li mfr . stock no . fb1056te li li motor type psc li li mounting cradle stud li li nema iec frame 48y li li nominal efficiency 0.65 li li overall length 13 3 4 li li rotation cw ccw li li rpm range 1001 1100 li li service factor 1.0 li li shaft length 5 li li shaft orientation up li li shaft type double flat li li voltage 208 230 460 li li standards ul recognized e46412 e44549 csa certified lr43341 lr4642 li li frame 48y li li resilient ring dia . in . 2 1 4 li li body dia . 5 5 8 li li stud quantity 4 li li stud size 8 32 x 1 1 2 li li shaft dia . 1 2 li li length less shaft 8 3 4 li li max . ambient temp . 40 degrees c li li ring to ring center 8 5 16 li li stud pattern 3 5 8 x 3 5 8 li li resilient ring dia . 2 1 4 li li motor application hvac r li li motor sub application condenser fan li ul
century