ceiling fans
dayton 6ele8 2.5 ton fan coil 3 pos flex 17.5 in x13
single piece air handler 3 position nominal capacity 2.5 tons rated cfm 0.5 in wc high 941 voltage 230 height 46 in . width 17 1 2 in . depth 21 1 2 in . supply opening width 10 3 8 in . supply opening depth 14 5 8 in . return air opening width 13 7 8 in . return air opening depth 18 7 8 in . use with heater models s1 4hk liquid line size 3 8 ods in . suction line size 3 4 ods in . br b features b ul li depth in . 21 1 2 li li height in . 46 li li includes drain pan li li item single piece air handler li li max . fuse size 15 li li min . circuit amps 3.5 li li phase 1 li li type 3 position not for downflow li li width in . 17 1 2 li li filter size 16x20x1 li li hz 60 li li use with heater models 6elj2 6elj3 6elj4 6elj5 li li voltage 230 li li manufacturers warranty length 10 yr parts 10 yr coil warranty requires online registration within 90 days of installation or warranty reverts to 5 yr parts 5 yr coil li li nominal capacity tons 2.5 li li supply opening width in . 10 3 8 li li supply opening depth in . 14 5 8 li li liquid line size in . 3 8 li li suction line size in . 3 4 li li return air opening width in . 13 7 8 li li return air opening depth in . 18 7 8 li li rated cfm 0.5 in wc high 941 li ul