appliance air filters
air handler 33e939 100 % synthetic media 24x24x12 v bank air filter
v bank air filter with gasket nominal filter size 24x24x12 nominal height 24 in . nominal width 24 in . nominal depth 12 in . filter efficiency 95 percent dop merv 16 air flow 500 fpm initial resistance 0.77 in . wc final resistance 1.5 in . wc filter pack enclosure plastic frame material fiberglass max . air flow 3000 cfm media area 193 sq. ft. max . temp . 150 degrees f standards ul 900 product has merv rating of 13 or higher br b features b ul li merv 16 li li item v bank air filter li li air flow 500 fpm li li max . temp . 150 degrees f li li nominal width 24 li li nominal height 24 li li media area 193 sq. ft. li li max . air flow 3000 cfm li li final resistance 1.5 wc li li initial resistance 0.77 wc li li filter pack enclosure plastic frame li li standards ul 900 li li nominal depth 12 li li filter efficiency 95 % dop li li green environmental attribute product has merv rating of 13 or higher li li nominal filter size 24x24x12 li li material fiberglass li li with without gasket with gasket li ul