appliance air filters
air handler 11z793 100 % synthetic media 20x20x12 v bank air filter
v bank air filter without gasket nominal filter size 20x20x12 nominal height 20 in . nominal width 20 in . nominal depth 12 in . filter efficiency 75 percent merv 11 air flow 500 625 750 fpm initial resistance 0.20 0.30 0.41 in . wc final resistance 1.5 in . wc filter pack enclosure metal frame material fiberglass max . air flow 2190 cfm media area 135 sq. ft. max . temp . 150 degrees f standards ul 900 br b features b ul li item v bank air filter li li material fiberglass li li max . temp . 150 degrees f li li air flow 500 625 750 fpm li li merv 11 li li filter pack enclosure metal frame li li standards ul 900 li li nominal height 20 li li nominal width 20 li li nominal depth 12 li li filter efficiency 75 % li li final resistance 1.5 wc li li initial resistance 0.20 0.30 0.41 wc li li max . air flow 2190 cfm li li media area 135 sq. ft. li li nominal filter size 20x20x12 li li with without gasket without gasket li ul