patio heaters
friedrich m12yj split system heat pump 11 200 13 300
split system heat pump indoor outdoor indoor outdoor mounting type wall btuh cooling 11200 reverse cycle heat btuh 13300 voltage 230 208 seer 21.5 hz 60 phase 1 min . circuit amps 10 max . time delay fuse amps 15 hspf 11 dehumidification 3 operation mode heat cool cfm high 353 cfm medium 272 cfm low 212 indoor sound level db 19 24 33 39 outdoor sound level db 45 filter type washable indoor width 35 1 4 in . indoor depth 8 1 4 in . indoor height 11 1 4 in . br b features b ul li includes indoor unit outdoor unit remote control li li item split system heat pump li li max . time delay fuse amps 15 li li min . circuit amps 10 li li phase 1 li li reverse cycle heat btuh 13300 li li seer 21.5 li li cfm high 353 li li cfm low 212 li li cfm medium 272 li li connection flare li li btuh cooling 11200 li li filter type washable li li hspf 11 li li hz 60 li li mounting type wall li li operation mode heat cool li li voltage 230 208 li li indoor outdoor indoor outdoor li li standards ahri etl cetl li li requires refrigerant line set for new installation li li precharged with r 410a li li indoor sound level db 19 24 33 39 li li outdoor sound level db 45 li li green environmental attribute product contributes to reducing water consumption li li green certification or other recognition energy star rated li li dehumidification 3 li li indoor depth 8 1 4 li li indoor height 11 1 4 li li indoor width 35 1 4 li li line size discharge o.d. 1 4 li li line size suction o.d. 3 8 li li outdoor depth 11 5 16 li li outdoor height 21 5 16 li li outdoor width 30 5 16 li li refrigeration line max . l 65 ft. li ul
friedrich