timers
honeywell l4081a1023 dual aquastat controller spst
dual aquastat controller spst low limit height 4 in depth 2 2 3 in width 3 7 8 in temp range 130 240 f differential 10 fixed full load amps 120v 8 locked rotor amps 120v 48 full load amps 240vac 5.1 locked rotor amps 240v 30.6 24v or 120v burner control circuit burner control circuit 120v 8 a burner control circuit 24v 5.1 a horizontal mounting high and low limit includes 3 4 in spud 14 npt br b features b ul li application high and low limit li li bulb size in . li li burner control circuit 120v a 8.0 li li burner control circuit 24v a 5.1 li li depth in . 2 2 3 li li full load amps 120v 8 li li full load amps 240vac 5.1 li li height in . 4 li li humidity range % rh non condensing 0 to 95 li li includes li li insulation depth in . 15 li li item dual aquastat controller li li locked rotor amps 120v 48 li li locked rotor amps 240v 30.6 li li temp . range high limit 130 degrees to 240 degrees f low limit 110 degrees to 220 degrees f li li type high and low limit li li width in . 3 7 8 li li differential high limit 10 degrees f fixed low limit 10 degrees to 25 degrees f adj. li li millvolt 025 a 025 to 12 vdc li li mounting horizontal li li system switching spst li li burner control circuit 24v or 120v li li agency compliance ul & csa li li requires 3 4 spud 14 npt li li spud size in . 3 4 to 14 npt li ul
honeywell