patio heaters
dayton 5pv60 hydronic unit heater 283800 btuh output 200 f water
hydronic unit heater heater type water steam output 2 psi steam 283800 btuh output 200 f water 205400 btuh air flow 4430 cfm motor hp 1 2 5.4 amps inlet outlet npt 2 in . height 15 1 4 in . width 37 1 2 in . depth 37 1 2 in . air flow direction vertical voltage 115 60 hz 1 phase max . operating psi 75 max . operating temp . 320 degrees f motor enclosure totally enclosed mounting height 21 ft. standards etl certified br b features b ul li cfm 4430 li li depth 37 1 2 li li depth in . 37 1 2 li li height 15 1 4 li li height in . 15 1 4 li li inlet outlet npt in . 2 li li item hydronic unit heater li li max . operating psi 75 li li motor hp 1 2 li li mounting height ft. 21 li li output 200 f water btuh 205400 li li output 2 psi steam btuh 283800 li li phase 1 li li type water steam li li width 37 1 2 li li width in . 37 1 2 li li air flow 4430 cfm li li hz 60 li li max . operating temp . 320 degrees f li li motor enclosure totally enclosed li li supply and return connection 2 li li voltage 115 li li agency compliance etl certified li li heater type water steam li li max . operating temp . f 320 li li standards etl certified li li amps 5.4 li li air flow direction vertical li li mounting height 21 ft. li li inlet outlet npt 2 li li output 2 psi steam 283800 btuh li li output 200 f water 205400 btuh li ul