appliance air filters
air handler 11z806 100 % synthetic media 24x24x12 v bank air filter
v bank air filter without gasket nominal filter size 24x24x12 nominal height 24 in . nominal width 24 in . nominal depth 12 in . filter efficiency 95 percent merv 15 air flow 500 625 750 fpm initial resistance 0.34 0.45 0.57 in . wc final resistance 1.5 in . wc filter pack enclosure plastic frame material fiberglass max . air flow 3000 cfm media area 193 sq. ft. max . temp . 150 degrees f standards ul 900 product has merv rating of 13 or higher br b features b ul li actual depth in . 11 1 2 li li actual height in . 23 3 8 li li actual width in . 23 3 8 li li case quantity 1 li li initial resistance in . wc 0.34 0.45 0.57 li li item v bank air filter li li material 100 % synthetic media li li max . air flow fpm 750 li li max . temp . 150 degrees f li li max . temp . f 150 li li nominal depth in . 12 li li nominal height in . 24 li li nominal width in . 24 li li package quantity 1 li li air flow 500 625 750 fpm li li air flow fpm 500 625 750 li li capacity cfm 2000 2500 3000 li li filter efficiency % 95 li li media area sq. ft. 193 li li merv 15 li li agency compliance ul 900 li li filter pack enclosure plastic frame li li standards ul 900 li li final resistance in . wc 1.5 li li nominal height 24 li li nominal width 24 li li green environmental attribute product has merv rating of 13 or higher li li nominal depth 12 li li final resistance 1.5 wc li li initial resistance 0.34 0.45 0.57 wc li li max . air flow 3000 cfm li li filter efficiency 95 % li li media area 193 sq. ft. li li nominal filter size 24x24x12 li li with without gasket without gasket li ul