cabinets
dayton 6wzn5 in line cabinet fanlow profile186 cfm
in line ventilator insulated yes voltage 115vac 60 hz 1 phase full load amps 2.20 number of speeds 1 watts 173 motor rpm 1100 motor type shaded pole motor enclosure open dripproof motor insulation class b max . inlet temp . 104 degrees f housing height 7 in . housing width 11 1 2 in . housing length 13 7 8 in . duct dia . 6 in . inlet height 3 1 4 in . inlet width 10 1 4 in . discharge dia . 6 in . mounting position horizontal housing material galvanized steel br b features b ul li cfm 0.000 in . sp 186 li li cfm 0.100 in . sp 184 li li cfm 0.125 in . sp 184 li li cfm 0.200 in . sp 183 li li cfm 0.250 in . sp 182 li li cfm 0.375 in . sp 181 li li cfm 0.500 in . sp 179 li li cfm 0.625 in . sp 175 li li cfm 0.750 in . sp 170 li li cfm 0.875 in . sp li li cfm 1.000 in . sp li li cfm 1.500 in . sp li li dimension a in . 13 7 8 li li dimension b in . 11 1 2 li li dimension c in . 7 15 16 li li dimension d in . 6 li li dimension e in . 1 1 4 li li dimension f in . 10 1 4 li li dimension g in . 3 1 4 li li for use with general ventilation applications li li full load amps 2.20 li li housing height in . 7 15 16 li li housing length in . 13 7 8 li li housing width in . 11 1 2 li li includes backdraft damper hardware and mounting brackets li li item in line ventilator li li motor rpm 1100 li li number of speeds 1 li li phase 1 li li sones 0.000 in . sp 5 ft. 3.0 li li sones 0.100 in . sp 5 ft. 3.0 li li sones 0.125 in . sp 5 ft. 3.0 li li sones 0.250 in . sp 5 ft. 3.0 li li type low profile li li wheel dia . in . 7 5 16 li li dimension b 11 1 2 li li housing material galvanized steel li li hz 60 li li motor enclosure open dripproof li li motor type shaded pole li li mounting position horizontal li li speed 1 li li speed control 48c172 li li voltage 115vac li li watts 173 li li cfm 1.250 in . sp li li agency compliance ul cul 507 amca air li li max . inlet temp . deg . f 104 li li wheel material polypropylene li li standards ul cul 507 amca air li li motor insulation class b li li dimension a 13 7 8 li li dimension d 6 li li dimension e 1 1 4 li li discharge height in . 3 1 4 li li discharge width in . 10 1 4 li li inlet width in . 3 1 4 li li inlet height in . 10 1 4 li li dimension f 10 1 4 li li insulated yes li li housing length 13 7 8 li li housing width 11 1 2 li li duct dia . 6 li li housing height 7 li li discharge dia . 6 li li max . inlet temp . 104 degrees f li li inlet height 3 1 4 li li inlet width 10 1 4 li li recommended accessories 48c172 li ul