ventilation fans
broan l900l fanin line900 cfm
in line ventilator voltage 120vac 60 hz 1 phase full load amps 3.00 watts 306 motor rpm 810 motor type permanent split capacitor motor enclosure open motor insulation class b max . inlet temp . 104 degrees f housing height 18 in . housing width 18 in . housing length 22 in . duct dia . 12 in . inlet height 8 in . inlet width 12 in . discharge height 8 in . discharge width 12 in . grille color housing material galvanized steel wheel material polymeric speed control 4c254 or 6e898 br b features b ul li cfm 0.000 in . sp 930 li li cfm 0.100 in . sp 902 li li cfm 0.125 in . sp 894 li li cfm 0.200 in . sp li li cfm 0.250 in . sp 853 li li cfm 0.375 in . sp 807 li li cfm 0.500 in . sp 754 li li cfm 0.625 in . sp 685 li li cfm 0.750 in . sp 587 li li cfm 0.875 in . sp li li cfm 1.000 in . sp 300 li li cfm 1.500 in . sp li li duct dia . in . 12 li li for use with general ventilation applications li li full load amps 3.00 li li housing height in . 18 li li housing length in . 22 li li housing width in . 18 li li includes automatic backdraft damper li li item in line ventilator li li motor rpm 810 li li phase 1 li li sones 0.000 in . sp 5 ft. 3.7 li li sones 0.100 in . sp 5 ft. 3.8 li li sones 0.125 in . sp 5 ft. 3.8 li li sones 0.250 in . sp 5 ft. 3.8 li li type in line li li wheel dia . in . 11 li li housing material galvanized steel li li hz 60 li li motor enclosure open li li motor type permanent split capacitor li li mounting position remote in line li li speed 1 li li speed control 4c254 or 6e898 li li voltage 120vac li li watts 306 li li cfm 1.250 in . sp li li agency compliance ul cul listed li li max . inlet temp . deg . f 104 li li wheel material polymeric li li standards ul cul listed li li grille color li li motor insulation class b li li discharge height in . 8 li li discharge width in . 12 li li inlet width in . 12 li li inlet height in . 8 li li housing length 22 li li housing width 18 li li duct dia . 12 li li housing height 18 li li max . inlet temp . 104 degrees f li li inlet height 8 li li discharge height 8 li li discharge width 12 li li inlet width 12 li ul
broan