space heaters
dayton 4lx66 unit heater ng 283 500 btuh 55 1 4w
long description br b features b ul li air temp . rise f 47 li li btuh input 350000 li li cfm 5600 li li flue dia . in . 6 li li full load amps 13.5 li li o.c. mounting in . 48 5 8 li li width in . 55 1 4 li li free air cfm 5600 li li btuh output 283500 li li agency compliance etl li li gas type ng li li ignition system hot surface pilot li li application 2000 above sea level require adjustments see owners manual li li installation height ft. 8 to 20 li li item gas unit heater li li type power vented direct drive propeller tubular heat exchanger li li voltage 120 li li manufacturers warranty length 1 yr . all components additional 9 yr . on heat exchanger flue collector and burners li li requires 24v thermostat li li depth in . 44 3 4 li li height in . 34 li li hz 60 li li gas connection in . 3 4 li li indoor air discharge height in . 24 1 2 li li indoor air discharge width in . 48 3 4 li li primary heat exchanger material 20 ga. aluminized steel li li depth 44 3 4 li li fan type propeller li li height 34 li li width 55 1 4 li li air flow 5600 cfm li li drive type direct li li standards etl li li burner air inlet size 6 li li vent power li li gas connection 3 4 li li air temp . rise 47 degrees f li li flue dia . 6 li li indoor air discharge height 24 1 2 li li indoor air discharge width 48 3 4 li li installation height 8 to 20 ft. li li o.c. mounting 48 5 8 li ul