cabinets
dayton 3dpe8 in line cabinet ventilator215 cfm115 v
in line ventilator singlewide insulated yes voltage 115vac 60 hz 1 phase full load amps 1.10 number of speeds 1 watts 100 motor rpm 1400 motor type permanent split capacitor motor enclosure open dripproof motor insulation class b max . inlet temp . 104 degrees f housing height 9 in . housing width 10 5 8 in . housing length 13 1 4 in . inlet height 9 1 4 in . inlet width 12 in . discharge height 6 in . discharge width 8 in . grille material grille color br b features b ul li cfm 0.000 in . sp 215 li li cfm 0.100 in . sp 202 li li cfm 0.125 in . sp 198 li li cfm 0.200 in . sp 187 li li cfm 0.250 in . sp 180 li li cfm 0.375 in . sp 159 li li cfm 0.500 in . sp 121 li li cfm 0.625 in . sp li li cfm 0.750 in . sp li li cfm 0.875 in . sp li li cfm 1.000 in . sp li li cfm 1.500 in . sp li li dimension a in . 13 1 4 li li dimension b in . 10 5 8 li li dimension c in . 10 1 2 li li dimension d in . 8 li li dimension e in . 6 li li dimension f in . 12 li li dimension g in . 9 1 4 li li for use with general ventilation applications li li full load amps 1.10 li li housing height in . 9 li li housing length in . 13 1 4 li li housing width in . 10 5 8 li li includes backdraft damper hardware and mounting brackets li li item in line ventilator li li motor rpm 1400 li li number of speeds 1 li li phase 1 li li sones 0.000 in . sp 5 ft. 1.7 li li sones 0.100 in . sp 5 ft. 1.4 li li sones 0.125 in . sp 5 ft. 1.7 li li sones 0.250 in . sp 5 ft. 1.9 li li type singlewide li li wheel dia . in . 5 1 4 li li dimension b 10 5 8 li li housing material galvanized steel li li hz 60 li li motor enclosure open dripproof li li motor type permanent split capacitor li li mounting position horizontal or vertical li li speed 1 li li speed control 48c172 li li voltage 115vac li li watts 100 li li cfm 1.250 in . sp li li agency compliance ul cul 507 amca air & sound li li max . inlet temp . deg . f 104 li li wheel material polypropylene li li standards ul cul 507 amca air li li grille color li li grille material li li motor insulation class b li li dimension a 13 1 4 li li dimension d 8 li li dimension e 6 li li discharge height in . 6 li li discharge width in . 8 li li inlet width in . 12 li li inlet height in . 9 1 4 li li dimension f 12 li li insulated yes li li housing length 13 1 4 li li housing width 10 5 8 li li housing height 9 li li max . inlet temp . 104 degrees f li li inlet height 9 1 4 li li discharge height 6 li li discharge width 8 li li inlet width 12 li li singlewide doublewide singlewide li li recommended accessories 6wzp2 48c172 li ul