furnaces
dayton 2ryr5 ng furnace 80 000 btuh 80plus efficiency
80 afue multi position gas furnace natural gas voltage 120 output btuh 64000 input 80000 btuh available cooling tons 1 1 2 to 4 additional features electronic hot surface ignition 100 percent shut off main gas valve psc four speed direct drive motor timed on adjustable off blower capability high level self diagnostics with fault code displays standard on integrated control module inducer rotates for easy conversion of venting options convertible to lp gas br b features b ul li afue % 80.0 li li available cooling tons 1 1 2 to 4 li li depth in . 29 1 2 li li flue dia . in . determined by length of run li li height in . 33 li li input btuh 80000 li li item 80 afue multi position furnace li li output btuh 64000 li li type natural gas li li width in . 21 li li additional features electronic hot surface ignition 100 percent shut off main gas valve psc four speed direct drive motor timed on adjustable off blower capability high level self diagnostics with fault code displays standard on integrated control module inducer rotates for easy conversion of venting options convertible to lp gas li li cfm .5 esp 1442 li li number of filters required side or bottom return 1 li li voltage 120 li li manufacturers warranty length heat exchanger 20 years residential 10 years commercial 5 years limited parts li li supply opening width in . 14 li li supply opening depth in . 23 li li agency compliance gama csa li li transformer rating 24v 40va li li side return filter size 16 x 25 li li bottom return filter size 20 x 25 li ul