ventilation fans
broan l400l fanin line400 cfm
in line ventilator voltage 120vac 60 hz 1 phase full load amps 1.4 watts 146 motor rpm 775 motor type permanent split capacitor motor enclosure open motor insulation class b max . inlet temp . 104 degrees f housing height 11 3 4 in . housing width 21 1 4 in . housing length 12 1 4 in . inlet height 4 1 2 in . inlet width 18 1 2 in . discharge height 4 1 2 in . discharge width 18 1 2 in . grille color housing material galvanized steel wheel material polymeric br b features b ul li cfm 0.000 in . sp 450 li li cfm 0.100 in . sp 415 li li cfm 0.125 in . sp 406 li li cfm 0.200 in . sp li li cfm 0.250 in . sp 360 li li cfm 0.375 in . sp 313 li li cfm 0.500 in . sp 271 li li cfm 0.625 in . sp 223 li li cfm 0.750 in . sp 167 li li cfm 0.875 in . sp li li cfm 1.000 in . sp 6 li li cfm 1.500 in . sp li li for use with general ventilation applications li li full load amps 1.4 li li housing height in . 11 3 4 li li housing length in . 12 1 4 li li housing width in . 21 1 4 li li includes automatic backdraft damper li li item in line ventilator li li motor rpm 775 li li phase 1 li li sones 0.000 in . sp 5 ft. 1.4 li li sones 0.100 in . sp 5 ft. 1.6 li li sones 0.125 in . sp 5 ft. 1.6 li li sones 0.250 in . sp 5 ft. 1.9 li li type in line li li wheel dia . in . 7 13 16 li li housing material galvanized steel li li hz 60 li li motor enclosure open li li motor type permanent split capacitor li li mounting position remote in line li li speed 1 li li speed control 4c331 or 6e897 li li voltage 120vac li li watts 146 li li cfm 1.250 in . sp li li agency compliance ul cul listed li li max . inlet temp . deg . f 104 li li wheel material polymeric li li standards ul cul listed li li grille color li li motor insulation class b li li discharge height in . 4 1 2 li li discharge width in . 18 1 2 li li inlet width in . 18 1 2 li li inlet height in . 4 1 2 li li housing length 12 1 4 li li housing width 21 1 4 li li housing height 11 3 4 li li max . inlet temp . 104 degrees f li li inlet height 4 1 2 li li discharge height 4 1 2 li li discharge width 18 1 2 li li inlet width 18 1 2 li ul
broan