appliance air filters
air handler 11z814 100 % synthetic media 20x20x12 v bank air filter
v bank air filter without gasket nominal filter size 20x20x12 nominal height 20 in . nominal width 20 in . nominal depth 12 in . filter efficiency 95 percent dop merv 16 air flow 500 625 fpm initial resistance 0.77 1.0 in . wc final resistance 1.5 in . wc filter pack enclosure metal frame material fiberglass max . air flow 1831 cfm media area 135 sq. ft. max . temp . 150 degrees f standards ul 900 product has merv rating of 13 or higher br b features b ul li merv 16 li li item v bank air filter li li green environmental attribute product has merv rating of 13 or higher li li air flow 500 625 fpm li li standards ul 900 li li max . temp . 150 degrees f li li nominal width 20 li li nominal height 20 li li nominal depth 12 li li filter efficiency 95 % dop li li media area 135 sq. ft. li li max . air flow 1831 cfm li li final resistance 1.5 wc li li initial resistance 0.77 1.0 wc li li filter pack enclosure metal frame li li nominal pleat 95 % li li nominal filter size 20x20x12 li li material fiberglass li li with without gasket without gasket li ul