patio heaters
precision coils w1021212n heating coil600cfm3 .8 gpm4x14x14
heating coil fluid type hot water air flow 600 cfm flow capacity 3.8 gpm casing length 14 in . casing depth 4 in . casing height 14 in . face area 1 sq. ft. supply and return connection 3 4 in . connection type mpt copper number of feeds 1 casing type flanged casing material 16 ga. galvanized steel number of rows 2 coils per bank 1 fin type sine fin material aluminum fin length 12 in . fin thickness 0.006 in . fin height 12 in . fins per inch 10 tube material copper br b features b ul li item heating coil li li number of feeds 1 li li number of rows 2 li li type hot water li li air flow 600 cfm li li flow capacity 3.8 gpm li li supply and return connection 3 4 li li total capacity 37.1 mbh li li tube material copper li li weight 15 lbs li li fin material aluminum li li tube outside dia . 5 8 li li fluid type hot water li li air flow rate 600 li li fins per inch 10 li li casing depth 4 li li casing height 14 li li casing length 14 li li casing material 16 ga. galvanized steel li li casing type flanged li li coils per bank 1 li li connection type mpt copper li li entering dry bulb 55 degrees f li li face area 1 sq. ft. li li fin height 12 li li fin length 12 li li fin thickness 0.006 li li fin type sine li li tube wall thickness 0.2 li li leaving dry bulb 112.1 degrees f li li air pressure drop 0.2 psi li ul