coffee & tea urns
bussmann bspm4208wyngr ul spd 4pole 120 208v remote
surge protection device type 4 location type type 2 nominal discharge current 20ka voltage 120 208 phase 3y wire 5 number of poles 4 max . surge current per phase 40ka max . surge current per mode 40ka max . continuing operating voltage 275 550vac voltage protection rating 1kv 1.8 kv short circuit current rating 200ka modes of protection l n n gnd mounting style din railenclosure type ip20wire gauge 2 14 awglength 3.93 width 2.83 depth 2.56 br b features b ul li depth 2.56 li li enclosure type ip20 li li includes installation instructions li li item surge protection device li li length 3.93 li li number of poles 4 li li phase 3y li li type type 4 li li width 2.83 li li mounting style din rail li li voltage 120 208 li li wire 5 li li wire gauge 2 14 awg li li standards ul 1449 3rd edition curus rohs compliant li li location type type 2 li li green environmental attribute not applicable li li green certification or other recognition rohs compliant li li modes of protection l n n gnd li li voltage protection rating 1kv 1.8 kv li li nominal discharge current 20ka li li max . continuing operating voltage 275 550vac li li short circuit current rating 200ka li li max . surge current per phase 40ka li li max . surge current per mode 40ka li ul
bussmann