air conditioners
century 9687 room air conditioner motorspscopen air over1550 rpm
room air conditioner motor permanent split capacitor open air over continuous 1 4 hp 1550 nameplate rpm voltage 115 48y frame service factor 1.0 60 50 hz full load amps 4.9 thermal protection auto insulation class b max . ambient temp . 40 degrees c number of speeds 3 ccwle rotation 1 phase stud mounting sleeve bearings body dia . 5 5 8 in . length less shaft 5 in . shaft type flat shaft dia . 1 2 in . shaft length 7 1 2 in . stud pattern 3 5 8 x 3 5 8 in . br b features b ul li application room air conditioners evaporative cooloers remote fan coils and other shaft mounted fan and blower applications li li base mounting centers in . 2 1 4 li li body dia . in . 5 5 8 li li bolt circle dia . in . 5 3 16 li li full load amps 4.9 li li hp 1 4 li li item room air conditioner motor li li length less shaft in . 5 li li nameplate rpm 1550 li li number of speeds 3 li li phase 1 li li shaft dia . in . 1 2 li li shaft length in . 7 1 2 ea . li li stud pattern in . 3 5 8 x 3 5 8 li li stud size in . 8 32 x 1 5 8 li li thermal protection auto li li ambient c 40 li li bearings sleeve li li capacitor required mfr . no. 2mdv3 li li duty continuous air over li li enclosure open air over li li footnotes 24 li li hz 60 50 li li insulation class b li li motor type psc li li mounting ring stud li li nema iec frame 48y li li rotation ccwle li li rpm range 1501 1600 li li service factor 1.0 li li shaft length 7 1 2 li li shaft type double li li voltage 115 li li lug location in . ao smith li li lead length in . 36 li li standards ul csa li li frame 48y li li resilient ring dia . in . 2 1 4 li li bolt circle dia . 5 3 16 li li body dia . 5 5 8 li li stud size 8 32 x 1 5 8 li li shaft dia . 1 2 li li length less shaft 5 li li max . ambient temp . 40 degrees c li li lead length 36 li li stud pattern 3 5 8 x 3 5 8 li li resilient ring dia . 2 1 4 li li motor application hvac r li li motor sub application room air conditioner li ul
century