ceiling fans
peco ta170 001 fan coil t statfan non staged 3 speed
fan coil t stat 2 pipe or 4 pipe switch type 6 relays switch action open or close number of switches 4 input 6 output fan switching non staged 3 speed system switching auto heat cool off control range 50 to 90 f differential configurable 3 deg . f sensor type local or remote color white display digital lcd voltage 24 to 277 vac number of stages 1 temp . settings per day 1 includes hardware br b features b ul li application 2 or 4 pipe auto heat cool 3 speed fan with on auto fan switch li li capillary length in . li li color white li li control range f 50 to 90 li li depth in . 1 1 2 li li differential deg . f configurable 3 li li enclosure type plastic li li full load amps 120v 5.8 li li full load amps 240vac 2.9 li li height in . 4 1 2 li li includes hardware li li insertion depth in . li li item fan coil thermostat li li locked rotor amps 120v 34.8 li li locked rotor amps 240v 17.4 li li number of stages 1 li li number of switches 4 input 6 output li li sensing bulb dia . in . li li sensing bulb length in . li li temp . settings per day 1 li li type low or line voltage li li width in . 5 2 3 li li display digital lcd li li input voltage 24 to 277 li li mounting position horizontal li li sensor type local or remote li li special information auto or manual heat to cool changeover key pad lockout li li switch action open or close li li switch type 6 relays li li fan switching nonstaged 3 speed li li system switching auto heat cool off li li uses commercial hvac applications li li voltage 24 to 277 vac li li agency compliance ul li li rated for pilot duty yes 24va li ul