ventilation fans
hankison hprp200 compressed air dryer200 cfm 38f50 hp
compressed air dryer iso class 5 200 cfm dew point 42 degrees f max . air compressor hp 50 max . pressure 232 psi pipe size 1 1 2 in . npt voltage 460vac 3 phase 7.5 full load amps power 1.26 kw max . inlet temp . 120 degrees f max . ambient temp . 110 degrees f r 134a refrigerant integral 3 micron filter epoxy powder coated finish 316 stainless steel heat exchanger material overall height 39 in . overall width 34 in . overall depth 32 in . br b features b ul li amps ac 7.50 li li cfm 200 li li depth in . 32 li li features monitor with electric demand drain and search mode li li finish epoxy powder coated li li full load amps 7.5 li li height in . 39 li li includes emm tm energy management monitor electric demand drain li li inlet outlet in . 1 1 2 npt li li item compressed air dryer li li max . air compressor hp 50 li li overall depth 32 li li phase 3 li li type refrigerated li li width in . 34 li li max . ambient temp . f 110 li li max . pressure psi 232 li li overall height 39 li li overall width 34 li li pipe size 1 1 2 npt li li power 1.26 kw li li refrigerant r 134a li li voltage 460vac li li heat exchanger fully insulated 316 stainless steel brazed plate li li max . inlet temp . deg . f 120 li li filter integral 3 micron li li dew point deg . f 42 li li max . pressure 232 psi li li iso class 5 li li heat exchanger material 316 stainless steel li li dew point 42 degrees f li li max . ambient temp . 110 degrees f li li max . inlet temp . 120 degrees f li ul