cabinets
dayton 6wzn7 in line cabinet fan 447 cfm
in line ventilator singlewide insulated yes voltage 115vac 60 hz 1 phase full load amps 1.87 number of speeds 1 watts 135 motor rpm 1000 motor type shaded pole motor enclosure open dripproof motor insulation class b max . inlet temp . 104 degrees f housing height 14 1 2 in . housing width 14 3 8 in . housing length 18 in . inlet height 13 1 4 in . inlet width 16 7 8 in . discharge height 8 in . discharge width 8 in . mounting position horizontal or vertical br b features b ul li cfm 0.000 in . sp 447 li li cfm 0.100 in . sp 441 li li cfm 0.125 in . sp 403 li li cfm 0.200 in . sp 380 li li cfm 0.250 in . sp 364 li li cfm 0.375 in . sp 317 li li cfm 0.500 in . sp 217 li li cfm 0.625 in . sp li li cfm 0.750 in . sp li li cfm 0.875 in . sp li li cfm 1.000 in . sp li li cfm 1.500 in . sp li li dimension a in . 18 li li dimension b in . 14 3 8 li li dimension c in . 14 1 2 li li dimension d in . 8 li li dimension e in . 8 li li dimension f in . 16 7 8 li li dimension g in . 13 1 4 li li for use with general ventilation applications li li full load amps 1.87 li li housing height in . 14 1 2 li li housing length in . 18 li li housing width in . 14 3 8 li li includes backdraft damper hardware and mounting brackets li li item in line ventilator li li motor rpm 1000 li li number of speeds 1 li li phase 1 li li sones 0.000 in . sp 5 ft. 1.5 li li sones 0.100 in . sp 5 ft. 1.5 li li sones 0.125 in . sp 5 ft. 1.5 li li sones 0.250 in . sp 5 ft. 2.0 li li type singlewide li li wheel dia . in . 7 1 8 li li dimension b 14 3 8 li li housing material galvanized steel li li hz 60 li li motor enclosure open dripproof li li motor type shaded pole li li mounting position horizontal or vertical li li speed 1 li li speed control 48c172 li li voltage 115vac li li watts 135 li li cfm 1.250 in . sp li li agency compliance ul cul 507 amca air li li max . inlet temp . deg . f 104 li li wheel material galvanized steel li li standards ul cul 507 amca air li li motor insulation class b li li dimension a 18 li li dimension d 8 li li dimension e 8 li li discharge height in . 8 li li discharge width in . 8 li li inlet width in . 16 7 8 li li inlet height in . 13 1 4 li li dimension f 16 7 8 li li insulated yes li li housing length 18 li li housing width 14 3 8 li li housing height 14 1 2 li li max . inlet temp . 104 degrees f li li inlet height 13 1 4 li li discharge height 8 li li discharge width 8 li li inlet width 16 7 8 li li singlewide doublewide singlewide li li recommended accessories 6wzp3 48c172 li ul