air conditioners
friedrich sh24m20 hazardous location a c 24k btu
hazardous location air conditioner 23700 24000 btuh voltage 208 230 2788 2727 watts eer 8.8 8.5 13.5 12.6 amps hz 60 ; 50 dehumidification 80 high cfm 600 control type mechanical fan speeds cooling 1 fan only speeds 1 air flow direction 8 width 25 15 16 in . depth 27 3 8 in . height 17 15 16 in . max . wall thickness 6 in . max . window width 42 in . min . window width 27 3 8 in . min . window height 18 in . sleeve yes chassis type slide out color white refrigerant type r410a br b features b ul li btuh 23700 24000 li li color white li li depth 27 3 8 li li eer 8.8 8.5 li li height 17 15 16 li li includes sleeve and chassis li li item hazardous location air conditioner li li remarks certified isa 12.12.01 and nfpa 70 ansi ul 484 room air conditioners . features electrofin 5 stage e coat on condenser coil and dual rated for 60 50 hz . li li width 25 15 16 li li control type mechanical li li high cfm 600 li li hz 60 ; 50 li li voltage 208 230 li li watts 2788 2727 li li refrigerant type r410a li li standards ul cul article 501 class 1 div2 group a and b class 1 div 2 group b class 1 div group c class 1 div 2 group d article 505 class 1 zone 2 group 11c class 1 zone 2 group 11b plus hydrogen or h2 class 1 zone 2 group 11b class 1 zone 2 group 11a li li sleeve yes li li chassis type slide out li li amps 13.5 12.6 li li fan speeds cooling 1 li li fan only speeds 1 li li air flow direction 8 li li max . wall thickness 6 li li min . window height 18 li li min . window width 27 3 8 li li max . window width 42 li li dehumidification 80 li ul
friedrich