ventilation fans
fantech pb370 2 exhaust fan kit8 5 8 in . lball1 in . w
exhaust fan kit housing material galvanized steel fits duct dia . 6 in . voltage 120 max . amps 1.02 max . wattage 120 number of speeds 1 housing dia . 13 1 8 in . length 8 5 8 in . cfm duct 370 cfm 0.000 in . sp 418 cfm 0.100 in . sp 394 cfm 0.200 in . sp 370 max . inlet temp . 140 degrees f inlet and outlet dia . 6 in . 60 hz 1 phase motor hp 1 6 motor rpm 2350 motor enclosure totally enclosed flange width 1 in . speed control mfr . no. 1dgv1 mfr . no . vt 20m or mfr . no . vt 20a br b features b ul li bearing type ball li li cfm 0.000 in . sp 418 li li cfm 0.100 in . sp 394 li li cfm 0.200 in . sp 370 li li cfm 0.400 in . sp 317 li li cfm 0.600 in . sp 268 li li cfm 0.800 in . sp 224 li li cfm 1.000 in . sp 186 li li cfm 1.500 in . sp 101 li li cfm duct 370 li li flange width in . 1 li li housing dia . in . 13 3 8 li li includes 1 centrifugal fan with mounting bracket 2 ceiling grilles 2 grille housings with dampers and y adapter li li inlet and outlet dia . in . 6 li li item exhaust fan kit li li length 8 5 8 li li length in . 8 5 8 li li max . amps 1.02 li li motor hp 1 6 li li motor rpm 2350 li li number of speeds 1 li li phase 1 li li type remote mounted in line li li housing material galvanized steel li li hz 60 li li max . wattage 120 li li motor enclosure totally enclosed li li mounting position horizontal or vertical li li speed control mfr . no. 1dgv1 mfr . no . vt 20m or mfr . no . vt 20a li li voltage 120 li li agency compliance culus li li max . inlet temp . deg . f 140 li li standards c ul us li li fits duct dia . in . 6 li li flange width 1 li li fits duct dia . 6 li li inlet and outlet dia . 6 li li housing dia . 13 1 8 li li green environmental attribute product contributes to reducing energy consumption li li green certification or other recognition energy star rated li li max . inlet temp . 140 degrees f li ul
fantech