cabinets
dayton 6wzn9 in line cabinet fan 813 cfm
in line ventilator singlewide insulated yes voltage 115vac 60 hz 1 phase full load amps 3.77 number of speeds 1 watts 405 motor rpm 1600 motor type permanent split capacitor motor enclosure open dripproof motor insulation class b max . inlet temp . 104 degrees f housing height 14 1 2 in . housing width 14 3 8 in . housing length 18 in . inlet height 13 1 4 in . inlet width 16 7 8 in . discharge height 8 in . discharge width 10 in . mounting position horizontal or vertical br b features b ul li cfm 0.000 in . sp 813 li li cfm 0.100 in . sp 784 li li cfm 0.125 in . sp 777 li li cfm 0.200 in . sp 755 li li cfm 0.250 in . sp 742 li li cfm 0.375 in . sp 707 li li cfm 0.500 in . sp 672 li li cfm 0.625 in . sp 638 li li cfm 0.750 in . sp 603 li li cfm 0.875 in . sp 567 li li cfm 1.000 in . sp 527 li li cfm 1.500 in . sp li li dimension a in . 18 li li dimension b in . 14 3 8 li li dimension c in . 14 1 2 li li dimension d in . 10 li li dimension e in . 8 li li dimension f in . 16 7 8 li li dimension g in . 13 1 4 li li for use with general ventilation applications li li full load amps 3.77 li li housing height in . 14 1 2 li li housing length in . 18 li li housing width in . 14 3 8 li li includes backdraft damper hardware and mounting brackets li li item in line ventilator li li motor rpm 1600 li li number of speeds 1 li li phase 1 li li sones 0.000 in . sp 5 ft. 3.0 li li sones 0.100 in . sp 5 ft. 3.0 li li sones 0.125 in . sp 5 ft. 3.0 li li sones 0.250 in . sp 5 ft. 3.0 li li type doublewide li li wheel dia . in . 7 1 2 li li dimension b 14 3 8 li li housing material galvanized steel li li hz 60 li li motor enclosure open dripproof li li motor type permanent split capacitor li li mounting position horizontal or vertical li li speed 1 li li speed control 48c172 li li voltage 115vac li li watts 405 li li cfm 1.250 in . sp li li agency compliance ul cul 507 amca air li li max . inlet temp . deg . f 104 li li wheel material polypropylene li li standards ul cul 507 amca air li li motor insulation class b li li dimension a 18 li li dimension d 10 li li dimension e 8 li li discharge height in . 8 li li discharge width in . 10 li li inlet width in . 16 7 8 li li inlet height in . 13 1 4 li li dimension f 16 7 8 li li insulated yes li li housing length 18 li li housing width 14 3 8 li li housing height 14 1 2 li li max . inlet temp . 104 degrees f li li inlet height 13 1 4 li li discharge height 8 li li discharge width 10 li li inlet width 16 7 8 li li singlewide doublewide doublewide li li recommended accessories 48c172 li ul