circuit breakers
plastec pla15ss2p blowerd d115 230 vhp 1 2
blower direct drive forward curve wheel dia 5.9 in cfm 0.500 in sp 550 cfm 0.750 in sp 540 72 dba 5 feet max inlet temp 140 deg f voltage 115 230 50 60 hz 1 phase full load amps 6.6 3.3 motor hp 1 2 height 16.13 in width 14.16 in depth 17.04 in inlet dia 4.92 in outlet dia 4.92 in housing material polypropylene includes motor mounting base br b features b ul li applications comments designed to exhaust fumes from highly corrosive environments such as laboratories chemical plants and hospitals li li bearing type ball li li blower rpm 3450 li li cfm 0.200 in . sp li li cfm 0.250 in . sp li li cfm 0.500 in . sp 550 li li cfm 0.750 in . sp 540 li li cfm 1.000 in . sp 500 li li cfm 1.500 in . sp 440 li li cfm 2.000 in . sp 310 li li dba 5 feet 72 li li depth in . 17.04 li li full load amps 6.6 3.3 li li height in . 16.13 li li housing material gray and green polypropylene li li hz 50 60 li li includes motor mounting base li li inlet dia . in . 4.92 li li item blower li li max . ambient temp . f 102 li li motor enclosure totally enclosed fan cooled li li motor frame 71 li li motor hp 1 2 li li motor rpm 3450 li li motor type capacitor run li li outlet dia . in . 4.92 li li phase 1 li li rotation ccw li li shaft dia . in . 14 mm li li type direct drive forward curve li li voltage 115 230 li li wheel dia . in . 5.90 li li wheel type forward curve li li wheel width in . 5.92 li li width in . 14.16 li li cfm 1.250 in . sp 475 li li agency compliance motors are ul listed and csa certified li li max . inlet temp . deg . f 140 li li wheel material polypropylene li li cfm 0.000 in . sp li li cfm 0.125 in . sp li li cfm 2.500 in . sp li li housing finish li li cfm 3.500 in . sp li li cfm 4.000 in . sp li li cfm 3.000 in . sp li ul
plastec