thermostats
honeywell t775u2006 line voltage thermostat 24 to 240vac
line voltage thermostat electronic universal control switch type 2 spdt switch action open close on rise number of switches 2 sensor type 1097 ohms ptc at 77f universal control with 1 universal input 1 temperature input 2 spdt relays 2 analog outputs reset option for use with heating cooling refrigeration color gray application various digital display enclosure type nema 1 24 to 240vac 9.8 a 4.9 a 58.8 a 29.4 a 10 125va vertical or horizontal 2 2 no br b features b ul li adjustable throttle range f 1 to 150 li li application various li li color gray li li control range f 40 to 248 li li depth 2 15 16 li li depth in . 2 15 16 li li differential deg . f 1 to 150 li li enclosure type nema 1 li li for use with heating cooling refrigeration li li full load amps li li full load amps 120v 9.8 a li li full load amps 240vac 4.9 a li li height 8 5 32 li li height in . 8 5 32 li li item line voltage thermostat li li locked rotor amps 120v 58.8 a li li locked rotor amps 240v 29.4 a li li number of relay inputs 2 li li number of relay outputs 2 li li number of switches 2 li li pilot duty contacts va 125va li li contact rating resistive 120v a 10 li li sensing bulb dia . in . 1 4 li li sensing bulb length in . 2 li li type electronic universal control li li width 4 13 32 li li width in . 4 13 32 li li 0 10v output no li li differential 1 degrees to 150 degrees f li li display digital li li display type digital li li input voltage li li mounting vertical or horizontal li li mounting type vertical or horizontal li li sensor type 1097 ohms ptc at 77f li li switch action open close on rise li li switch type 2 spdt li li voltage range 24 to 240vac li li agency compliance ul cul ce ip65 li li characteristics universal control with 1 universal input 1 temperature input 2 spdt relays 2 analog outputs reset option li li temp . sensitivity deg . f 1 li li control range 40 degrees to 248 degrees f li li temp . sensitivity 1 degrees f li li contact rating resistive 120v 10a li li adjustable throttle range 1 degrees to 150 degrees f li li sensing bulb dia . 1 4 li li sensing bulb length 2 li ul
honeywell