water transfer pumps
honeywell l4008a1015 aquastat controller
line voltage thermostat remote bulb temperature control switch type spst switch action open on rise number of switches 1 sensor type copper bulb totally enclosed micro switch tm requires immersion well or bulb compression fitting for new installations for use with regulating temperature of air or liquids in ducts pipes tanks or boilers color gray application high or low limit aquastat controller analog display enclosure type slip on with set screw 120 to 240vac 8a 5a 8a br b features b ul li application high or low limit aquastat controller li li capillary length in . 66 li li color gray li li control range f 100 to 240 li li depth in . 2 1 8 li li differential deg . f 5 to 30 li li enclosure type slip on with set screw li li for use with regulating temperature of air or liquids in ducts pipes tanks or boilers li li full load amps li li full load amps 120v 8a li li full load amps 240vac 5.1 a li li height in . 5 5 8 li li includes 5 1 2 ft capillary tube li li item line voltage thermostat li li locked rotor amps 120v 48a li li locked rotor amps 240v 30.6 a li li number of switches 1 li li pilot duty contacts va li li sensing bulb dia . in . 3 8 li li sensing bulb length in . 2 7 8 li li type remote bulb temperature control li li width in . 2 li li display analog li li inductive amps 120v 8a li li inductive amps 240v 5a li li input voltage li li mounting horizontal or vertical li li sensor type copper bulb li li switch action open on rise li li switch type spst li li voltage range 120 to 240vac li li agency compliance ul component recognized li li characteristics totally enclosed micro switch tm requires immersion well or bulb compression fitting for new installations li ul
honeywell