valves
red hat jb8214280csa gas solenoid valve 2 way nc alum 2 in
gas solenoid valve number of ways 2 configuration normally closed body material aluminum 2 pipe size in . 2 3 32 orifice dia . in . psi differential air inert gas 5 psi differential water 5 psi differential light oil 5 cv flow factor 55 2940500 fuel gas capacity btuh gpm max . 366.66 psi differential min . 0 psi differential max . 5 5 opd range psi 40 fluid ambient temp . min . f 125 max . fluid temp . f 125 fluid ambient temp . max . f watts 20 voltage 120 110 hz 60 50 br b features b ul li application for on off control of fuel gas in commercial and industrial gas burners li li btuh 2940500 li li coefficient of volume 55 li li construction reference no. 2 li li electrical connections 1 2 conduit with 18 leads li li fluid ambient temp . max . f 125 li li fluid ambient temp . min . f 40 li li fuel gas capacity btuh 2940500 li li gpm max . 366.66 li li height 7.63 li li item fuel gas solenoid valve with test port li li length 6.36 li li max . fluid temp . f 125 li li opd range psi 5 li li max . operating pressure differential light oil 5 li li max . operating pressure differential air inert gas 5 li li psi differential min . 0 li li max . operating pressure differential water 5 li li orifice dia . in . 2 3 32 li li pipe size in . 2 li li width 6.32 li li ambient temp . range 40 degrees to 125 degrees f li li body material aluminum li li configuration normally closed li li cv flow factor 55 li li hz 50 60 li li nema rating 1 li li overall height 7 5 8 li li overall length 6 3 8 li li overall width 6 5 16 li li pipe size 2 li li seal material nbr li li voltage 110 120vac li li watts 20 li li agency compliance ul csa safety shutoff valve li li coil enclosure general purpose junction box li li number of ways 2 li li center line pipe center size in . 5.85 li li standards ul csa for safety shutoff li li valve design 2 way 2 position li li coil insulation class f li li psi differential max . 5 li li coil key a li li max . fluid temp . 125 degrees f li li orifice dia . 2 3 32 li li center line pipe center size 5 7 8 li li valve configuration normally closed li li max . operating pressure differential 5 psi li li min . operating pressure differential 0 psi li ul