circuit breakers
square d la36400 circuit breaker plug in lug 600vac 400a 400a la
circuit breaker amps 400 number of poles 3 circuit breaker type standard ac voltage rating 600vac dc voltage rating 250vdc for use with i line panelboards series la trip type thermal magnetic terminal connection lug phase connection abc mounting plug in panelboard height 11 in . width 6 in . depth 5.8 in . min . wire size 1 awg al max . wire size 600 kcmil al 250 kcmil al instantaneous trip adjustable high amp trip setting 4000a low amp trip setting 2000a frame size 400a la br b features b ul li depth 5.8 li li depth in . 5.84 li li for use with i line panelboards li li height 11 li li item circuit breaker li li length in . 11.00 li li max . wire size awg 600 kcmil li li number of poles 3 li li phase 3 li li type panelboard mount li li width 6 li li width in . 6.00 li li air rating 22ka li li frame size 400a la li li high amp trip setting 4000a li li low amp trip setting 2000a li li min . wire size awg 1 li li mounting plug in panelboard li li phase connection abc li li series la li li terminal connection lug li li voltage 600vac li li circuit breaker type standard li li air 125vdc 10ka li li air 240vac 42ka li li air 480vac 30ka li li air 65vdc 10ka li li standards ul csa li li max . dc voltage v 250 li li air 120vac 42ka li li air 48vdc 10ka li li amps 400 li li instantaneous trip adjustable li li min . wire size 1 awg al li li max . wire size 600 kcmil al 250 kcmil al li li panelboard mounting plug in li li air 600vac 22ka li li ac voltage rating 600vac li li dc voltage rating 250vdc li li trip type thermal magnetic li ul
square d