valves
dayton 2a201 solenoid valve less coil 2way 1 1 4in nc
steam solenoid valve less coil body material brass 2 way normally closed pipe size 1 1 4 in . orifice dia . 1 1 4 in . coefficient of volume 16.00 min . operating pressure differential 5 psi max . operating pressure differential 150 psi safe working water pressure 300 psi safe working steam pressure 300 psi operation type pilot operated steam capacity 3951 lb . hr . gasket material ptfe max . fluid temp . 400 degrees f overall length 4 9 16 in . overall height 5 25 32 in . br b features b ul li coefficient of volume 16.00 li li construction reference no. 2 li li for use with dayton solenoid coils li li height 5 25 32 li li item steam solenoid valve less coil li li length 4 9 16 li li max . fluid temp . f 400 li li pressure differential max . 150 li li psi differential min . 5 li li orifice dia . in . 1 1 4 li li pipe size in . 1 1 4 li li safe working water psi 300 li li steam capacity lb . hr . 3951 li li width 3 li li body material brass li li configuration normally closed li li cv flow factor 16 li li gasket material ptfe li li operation type pilot operated li li overall height 5 25 32 li li overall length 4 9 16 li li pipe size 1 1 4 li li safe working steam psi 300 li li voltage 24vdc li li agency compliance csa nfpa ul li li coil enclosure nema type 1 li li number of ways 2 li li center line pipe center size in . 1 11 32 li li valve design 2 way li li coil insulation class h li li coil key a li li steam capacity 3951 lb . hr . li li max . fluid temp . 400 degrees f li li orifice dia . 1 1 4 li li valve configuration normally closed li li max . operating pressure differential 150 psi li li min . operating pressure differential 5 psi li li safe working water pressure 300 psi li li safe working steam pressure 300 psi li ul