ducting
soler & palau td 250 mixed flow duct fan
mixed flow duct fan housing material metal fits duct dia . 10 in . voltage 115 max . amps 2.2 max . wattage 241 162 number of speeds 2 housing dia . 10 3 4 in . length 11 1 2 in . cfm 0.000 in . sp 754 541 cfm 0.125 in . sp 715 475 cfm 0.250 in . sp 680 418 max . inlet temp . 140 degrees f inlet and outlet dia . 9 3 4 in . 60 hz 1 phase motor hp 1 3 motor rpm 3200 2400 motor enclosure totally enclosed flange width 1 1 2 in . speed control mfr . no. 1dgv1 housing finish epoxy br b features b ul li bearing type ball li li cfm 0.000 in . sp 754 541 li li cfm 0.125 in . sp 715 475 li li cfm 0.250 in . sp 680 418 li li cfm 0.375 in . sp 640 355 li li cfm 0.500 in . sp 606 295 li li cfm 0.750 in . sp 520 218 li li cfm 1.000 in . sp 405 170 li li cfm 1.500 in . sp 245 65 li li flange width in . 1 1 2 li li housing dia . in . 10 3 4 li li includes mounting bracket li li inlet and outlet dia . in . 9 3 4 li li item mixed flow duct fan li li length 11 1 2 li li length in . 11 1 2 li li max . amps 2.2 li li motor hp 1 3 li li motor rpm 3200 2400 li li number of speeds 2 li li phase 1 li li type in line 2 speed mixed flow li li housing finish epoxy li li housing material metal li li hz 60 li li max . wattage 241 162 li li motor enclosure totally enclosed li li mounting position horizontal or vertical li li speed control mfr . no. 1dgv1 li li voltage 115 li li agency compliance c ul us li li max . inlet temp . deg . f 140 li li standards c ul us li li fits duct dia . in . 10 li li flange width 1 1 2 li li fits duct dia . 10 li li inlet and outlet dia . 9 3 4 li li housing dia . 10 3 4 li li max . inlet temp . 140 degrees f li ul