air compressors
dayton 1lzp8 pump deep well 2 wire 5gpm 1 2hp 115v
pump deep well submersible number of wires 2 5 gpm 1 2 hp voltage 115 amps ac 12 1 phase stages 13 built in check valve pump material stainless steel impeller material celcon discharge port 1.25 in . flow ranges 2.5 7 gpm max . operating temp . 86 f pump motor shell stainless steel max . head 364 ft. well capacity low recommended tank 3ya56 1xhg8 br b features b ul li amps ac 12 li li discharge port in . 1.25 li li height in . li li hp 1 2 li li includes li li item pump li li length in . li li max . head ft. 364 li li number of wires 2 li li phase 1 li li shut off psi li li type deep well submersible li li width in . li li control box required li li gpm of water 100 ft 30 50 psi 6 5 li li gpm of water 40 ft 30 50 psi 7 li li gpm of water 60 ft 30 50 psi 7 6 li li gpm of water 80 ft 30 50 psi 7 6 li li flow ranges gpm 2.5 7 li li gpm 5 li li impeller material celcon li li motor franklin tm li li motor enclosure li li screen material stainless steel li li seal type li li sf amps li li shaft material 303 stainless steel li li gpm of water 20 ft 30 50 psi 7 li li stages 13 li li tank psi 2030405060 li li voltage 115 li li well capacity low li li max . operating temp . f 86 li li built in check valve yes li li pump bearings peek li li pump material stainless steel li li pump motor shell stainless steel li li gpm of water 125 ft 30 50 psi 6 5 li li gpm of water 150 ft 30 50 psi 5 4 li li gpm of water 175 ft 30 50 psi 4 3 li li gpm of water 200 ft 30 50 psi 4 2 li li gpm of water 250 ft 30 50 psi 2 li li gpm of water 300 ft 30 50 psi li li gpm of water 350 ft 30 50 psi li li gpm of water 400 ft 30 50 psi li li gpm of water 450 ft 30 50 psi li li gpm of water 500 ft 30 50 psi li li recommended tank 3ya56 1xhg8 li li gpm vertical depth to water 20 ft 30 psi li li gpm vertical depth to water 100 ft 30 psi 6 li li gpm vertical depth to water 200 ft 30 psi 4 li li gpm vertical depth to water 20 ft 50 psi 7 li li gpm vertical depth to water 100 ft 50 psi 5 li li gpm vertical depth to water 200 ft 50 psi 2 li li compliance certified for use in potable water applications in ca and vt li ul