water transfer pumps
liberty p382le51 sewage package 1 2 hp 115v 12amps
simplex sewage system below grade 1 2 hp wide angle piggy back switch voltage 115 60 hz 1 phase amps 12 inlet 4 in outlet 2 in vent 2 in gpm of water 10 ft. of head 118 max . temp 140 degrees f basin height 24 in basin dia 24 in basin capacity 41 gal . 2 in max . dia . solids 16 gauge 3 conductor cord size features quicktree technology with switch access cover allows easy field service of switch br b features b ul li gpm 17 ft. total head 68 li li hp 1 2 li li gpm 11.5 ft. total head 100 li li nema start code f li li rpm 1725 li li voltage 115 li li iapmo approved no li li phase 1 li li inlet 4 li li features quicktree technology with switch access cover allows easy field service of switch li li switch wide angle piggy back li li item simplex sewage system li li application sewage li li cord length 10 ft. li li cord size 16 gauge 3 conductor li li cover material structural foam li li cable entry rubber channel seal li li type below grade li li gpm of water 10 ft. of head 118 li li gpm of water 15 ft. of head 92 li li gpm of water 20 ft. of head 55 li li gpm of water 5 ft. of head 140 li li gpm of water 22 ft. of head 30 li li basin material polyethylene li li outlet 2 li li vent 2 li li amps 12 li li max . dia . solids 2 li li basin dia . 24 li li max . temp . 140 degrees f li li basin height 24 li li hz 60 li li basin capacity 41 gal . li li maximum head 24 ft. li ul
liberty