plumbing pumps
zoeller n161 pump effluent 1 2 hp
submersible effluent pump manual operation type 1 2 hp none base material cast iron housing cast iron top material cast iron carbon ceramic impeller material bronze 115v 15.5 amps height 18 9 16 in . 12 3 4 in . diameter cord length 20 ft. discharge npt 1 1 2 in . shaft seal carbon ceramic max . dia . solids 3 4 in . gpm of water 10 ft. of head 93 max . head 56 ft. max . temp . 130 degrees f 1 phase bearing type ball br b features b ul li base material cast iron li li bearing type ball li li cord length ft. 20 li li dia . in . 12 3 4 li li discharge npt in . 1 1 2 li li gpm of water 10 ft. of head 93 li li gpm of water 15 ft. of head 85 li li gpm of water 20 ft. of head 78 li li gpm of water 25 ft. of head 70 li li gpm of water 30 ft. of head 61 li li gpm of water 40 ft. of head 45 li li gpm of water 5 ft. of head 100 li li gpm of water 50 ft. of head 20 li li height 18 9 16 li li height in . 18 9 16 li li housing cast iron li li hp 1 2 li li item submersible effluent pump li li max . dia . solids in . 3 4 li li max . head ft. 56 li li max . temp . 130 degrees f li li mechanical seal carbon ceramic li li phase 1 li li thermal protection thermal protection li li type manual operation switch not included li li cord length 20 ft. li li duty intermittent li li impeller material bronze li li motor type psc li li operation type manual li li rpm 3450 li li shaft material carbon steel li li shaft seal carbon ceramic li li switch type none li li top material cast iron li li voltage 115v li li standards ul 778 csa c22 .2 108 li li amps 15.5 li li diameter 12 3 4 li li max . dia . solids 3 4 li li discharge npt 1 1 2 li li max . head 56 ft. li ul
zoeller