water heaters
rheem ruud gx90 550a water heater gas 90 gallon 550 000 btu
commercial gas water heater tank capacity 90 gal . fuel type natural gas 550000 btuh jacket dia . 30 in . draft hood size 10 in . height to top of vent connection 74 1 2 in . recovery 90 f rise 593 gph low nox burner yes voltage 120vac first hour recovery 596 gph max . pressure 160 psi temp . range 100 degrees to 180 degrees f vent type standard ignition type spark to pilot energy factor gas connection 1 in . top water connection size 2 in . height to top of heater 68 in . br b features b ul li btuh 550000 li li draft hood size in . 10 li li features can not be installed over altitude of 2000 ft. specialized burner assembly spark to pilot ignition system diagnostic system space saving design low profile automatic flu damper li li gas connection in . 1 li li gas type natural gas li li height cold side connection in . 25 li li height side hot connection in . 59 li li height to t & p opening in . 59 li li height top of heater in . 68 li li height top of vent connection in . 74 1 2 li li includes t and p relief valve full port full flow brass drain valve hand hole cleanout li li item commercial gas water heater li li jacket dia . in . 30 li li recovery 100 f rise gph 533 li li tank gal . 90 li li temp . range 100 degrees to 180 degrees f li li temp . range f 100 to 180 li li type gas li li vent type standard li li energy factor li li fuel type natural gas li li ignition type spark to pilot li li input btu 550000 li li max . pressure psi 160 li li recovery 90 f rise gph 593 li li tank capacity 90 gal . li li voltage 120vac li li manufacturers warranty length limited 3 yr . tank and 1 yr . parts li li standards ul certified meets ansi z21 .10.3 2001 requirements gama rated complies with scaqmd rule 1146.2 for lownox emissions li li recovery 50 f rise gph 1067 li li recovery 70 f rise gph 762 li li recovery 110 f rise gph 485 li li recovery 120 f rise gph 444 li li recovery 130 f rise gph 410 li li recovery 140 f rise gph 381 li li max . pressure 160 psi li li top water connection in . 2 li li side water connection in . 2 li li first hour recovery gph 596 li li compliance certified for use in potable water applications in ca and vt li li gas connection 1 li li draft hood size 10 li li first hour recovery 596 gph li li jacket dia . 30 li li recovery 100 f rise 533 gph li li recovery 110 f rise 485 gph li li recovery 120 f rise 444 gph li li recovery 130 f rise 410 gph li li recovery 140 f rise 381 gph li li recovery 50 f rise 1067 gph li li recovery 70 f rise 762 gph li li recovery 90 f rise 593 gph li li height to top of vent connection 74 1 2 li li low nox burner yes li li top water connection size 2 li li height to top of heater 68 li li height to cold side connection 25 li li height to hot side connection 59 li li side water connection size 2 li ul