water transfer pumps
dayton 4le22 submersible sewage pump 1 1 2 hp g2827246
submersible sewage pump automatic 1 1 2 hp switch type tether base material 303 stainless steel housing cast iron impeller material cast iron voltage 230 phase 1 amps 16 height 21 1 4 in . cord length 25 ft. discharge size 3 in . npt max . dia . solids 2 1 2 in . gpm of water 5 ft. of head 370 gpm of water 10 ft. of head 335 max . head 39 ft. max . temp . 77 degrees f thermal protection auto bearing type ball br b features b ul li hp 1 1 2 li li cord length ft. 25 li li gpm of water 5 ft. of head 370 li li on point in . 23.35 li li gpm of water 15 ft. of head 295 li li gpm of water 30 ft. of head 125 li li discharge npt in . 3 li li gpm of water 10 ft. of head 335 li li gpm of water 20 ft. of head 240 li li gpm of water 25 ft. of head 185 li li height in . 21 1 4 li li off point in . 14.35 li li phase 1 li li rpm 1750 li li bearing type ball li li thermal protection auto li li switch type tether li li shaft material sic li li motor type psc li li standards csa li li max . dia . solids in . 2 1 2 li li max . temp . f 104 li li type automatic li li max . head ft. 39 li li housing cast iron li li top material cast iron li li item submersible sewage pump li li dia . in . 16 3 4 li li shaft seal silicon carbide li li voltage 230 li li base material cast iron li li impeller material cast iron li li amps 16 li ul