valves
dayton 4a715 solenoid valve less coil 3 8 in nc brass
steam solenoid valve less coil body material brass 2 way normally closed pipe size 3 8 in . orifice dia . 3 8 in . coefficient of volume 2.20 min . operating pressure differential 2 psi max . operating pressure differential 150 psi safe working water pressure 350 psi safe working steam pressure 350 psi operation type pilot operated steam capacity 594 lb . hr . gasket material ptfe max . fluid temp . 400 degrees f overall length 2 3 8 in . overall height 3 5 16 in . br b features b ul li coefficient of volume 2.20 li li construction reference no. 4 li li for use with dayton solenoid coils li li height 3 5 16 li li item steam solenoid valve less coil li li length 2 3 8 li li max . fluid temp . f 400 li li pressure differential max . 150 li li psi differential min . 2 li li orifice dia . in . 3 8 li li pipe size in . 3 8 li li safe working water psi 350 li li steam capacity lb . hr . 594 li li width 1 3 16 li li body material brass li li configuration normally closed li li cv flow factor 2.20 li li gasket material ptfe li li operation type pilot operated li li overall height 3 5 16 li li overall length 2 3 8 li li pipe size 3 8 li li safe working steam psi 350 li li voltage 24vdc li li agency compliance csa nfpa ul li li coil enclosure nema type 1 li li number of ways 2 li li center line pipe center size in . 9 16 li li valve design 2 way li li coil insulation class h li li coil key a li li steam capacity 594 lb . hr . li li max . fluid temp . 400 degrees f li li orifice dia . 3 8 li li valve configuration normally closed li li max . operating pressure differential 150 psi li li min . operating pressure differential 2 psi li li safe working water pressure 350 psi li li safe working steam pressure 350 psi li ul