thermostats
johnson controls t26t 3c line voltage thermostat
line voltage thermostat heating cooling switch type spdt switch action open close on rise and open close on fall number of switches 2 sensor type bimetal color brown enclosure type nema 1 120 to 277vac br b features b ul li application electric heat line voltage li li color brown li li control range f 40 to 90 li li depth 3 li li depth in . 3 li li differential deg . f .7 li li enclosure type nema 1 li li full load amps 120v 15a li li full load amps 240vac 3a li li height 5 li li height in . 5 li li item line volt mechanical tstat li li locked rotor amps 120v 36a li li locked rotor amps 240v 18a li li number of relay inputs 1 li li number of relay outputs 1 li li number of stages 1 li li number of switches 2 li li pilot duty contacts va 125va li li type heating cooling li li width 3 li li width in . 3 li li 0 10v output no li li differential 0.7 degrees f li li inductive amps 120v 10a li li inductive amps 240v 10a li li input voltage 120 to 277vac li li mounting wall li li mounting location wall li li mounting type vertical or horizontal li li sensor type bi metal li li switch action open close on rise and open close on fall li li switch type spdt li li voltage range 24 to 277vac li li control range 40 degrees to 90 degrees f li li inductive amps 208v 10a li ul