valves
dayton 1a578 solenoid valve less coil 3 4 in nc brass
solenoid valve less coil body material brass 2 way normally closed pipe size 3 4 in . orifice dia . 3 4 in . coefficient of volume 5.50 min . operating pressure differential 5 psi max . operating pressure differential 125 psi safe working water pressure 300 psi operation type pilot operated flow range 12.3 to 61.5 gpm airflow 121 to 280 scfm gasket material buna n max . fluid temp . 180 degrees f overall length 2 13 16 in . overall height 3 3 4 in . for use with dayton solenoid coils br b features b ul li airflow scfm 280 121 li li coefficient of volume 5.50 li li construction reference no. 2 li li flow range 12.3 to 61.5 gpm li li for use with dayton solenoid coils li li gpm max . 61.5 li li height 3 3 4 li li item solenoid valve less coil li li length 2 13 16 li li max . fluid temp . f 180 li li min . flow rate gpm 12.3 li li pressure differential max . 125 li li psi differential min . 5 li li orifice dia . in . 3 4 li li pipe size in . 3 4 li li safe working water psi 300 li li width 2 5 16 li li body material brass li li configuration normally closed li li cv flow factor 5.50 li li gasket material buna n li li operation type pilot operated li li overall height 3 3 4 li li overall length 2 13 16 li li pipe size 3 4 li li voltage 24vac li li agency compliance csa nfpa ul li li coil enclosure nema 1x li li number of ways 2 li li center line pipe center size in . 11 16 li li valve design 2 way li li coil insulation class f li li max . psi differential air water 125 li li max . fluid temp . 180 degrees f li li orifice dia . 3 4 li li airflow 121 to 280 scfm li li valve configuration normally closed li li max . operating pressure differential 125 psi li li min . operating pressure differential 5 psi li li safe working water pressure 300 psi li ul