water transfer pumps
liberty 287 sump pump 1 2 hp
submersible sump pump 1 2 hp switch type vertical cord length 10 ft. 115 voltage 8.5 amps dia . 9 5 8 in . discharge npt 1 1 2 in . height 13 in . max . head 37 ft. max . dia . solids 3 4 in . gpm of water 5 ft. of head 62 gpm of water 10 ft. of head 55 gpm of water 15 ft. of head 47 gpm of water 20 ft. of head 38 gpm of water 25 ft. of head 28 gpm of water 30 ft. of head 17 max . temp . 140 degrees f min . sump pit dia . 10 in . off point 4 in . on point 9 1 2 in . br b features b ul li gpm of water 35 ft. of head 5 li li max . head ft. 37 li li mechanical seal crb cmc li li voltage 115 li li base material cast iron li li cord length ft. 10 li li dia . in . 9 5 8 li li gpm of water 10 ft. of head 55 li li gpm of water 20 ft. of head 38 li li gpm of water 25 ft. of head 28 li li max . dia . solids in . 3 4 li li motor type psc li li rpm 3450 li li shaft material 416 stainless steel li li top material polypropylene li li standards csa c us li li item submersible sump pump li li shaft seal buna n stainless steel li li gpm of water 30 ft. of head 17 li li type automatic li li off point in . 4 li li hp 1 2 li li height in . 13 li li discharge npt in . 1 1 2 li li gpm of water 15 ft. of head 47 li li gpm of water 5 ft. of head 62 li li housing cast iron li li thermal protection yes li li impeller material engineered polymer li li switch type vertical li li on point in . 9 1 2 li li max . temp . f 140 li li amps 10 li ul
liberty