water heaters
rheem ruud es50 18 g water heater commercial 50 gallon 240 volts
electric water heater commercial tank capacity 50 gal . voltage 240vac 1 or 3 phase 18000 total watts overall height 43 5 8 in . jacket dia . 26 1 4 in . overall width 32 in . recovery 90 f rise 83 gph recovery 50 f rise 149 gph recovery 70 f rise 106 gph recovery 100 f rise 74 gph recovery 110 f rise 68 gph recovery 120 f rise 62 gph recovery 130 f rise 57 gph recovery 140 f rise 53 gph height to cold side connection 4 3 4 in . br b features b ul li amps ac 43 li li front to back of heater in . 32 li li height cold side connection in . 4 3 4 li li height to t & p opening in . 36 1 4 li li height top of heater in . 43 5 8 li li height top of panel in . 36 1 8 li li includes full port full flow brass drain valve and t and p valve li li item electric water heater li li jacket dia . in . 26 1 4 li li number of elements 3 li li phase 1 or 3 li li recovery 100 f rise gph 74 li li tank gal . 50 li li temp . range 90 degrees to 160 degrees f preset 120 degrees f li li type commercial li li connection location side li li energy factor li li overall height 43 5 8 li li overall width 32 li li recovery 90 f rise gph 83 li li tank capacity 50 gal . li li total watts 18000 li li voltage 240vac li li manufacturers warranty length 3 yr . limited tank 1 yr . limited parts li li standards meets or exceeds standby loss requirements of ashrae meets ul sanitation nsf certified for 150 psi max working pressure li li water connection 1 1 2 npt li li recovery 50 f rise gph 149 li li recovery 70 f rise gph 106 li li recovery 110 f rise gph 68 li li recovery 120 f rise gph 62 li li recovery 130 f rise gph 57 li li recovery 140 f rise gph 53 li li max . pressure 150 psi li li compliance certified for use in potable water applications in ca and vt li li jacket dia . 26 1 4 li li recovery 100 f rise 74 gph li li recovery 110 f rise 68 gph li li recovery 120 f rise 62 gph li li recovery 130 f rise 57 gph li li recovery 140 f rise 53 gph li li recovery 50 f rise 149 gph li li recovery 70 f rise 106 gph li li recovery 90 f rise 83 gph li li height to cold side connection 4 3 4 li li height to hot side connection 43 5 8 li li residential commercial commercial li ul