ducting
fantech fg12xl inline centrifugal duct fan12 in . l
inline centrifugal duct fan housing material galvanized steel fits duct dia . 12 in . voltage 115 max . amps 3 max . wattage 326 number of speeds 1 housing dia . 16 in . length 8 15 16 in . cfm duct 940 cfm 0.000 in . sp 940 cfm 0.125 in . sp 903 cfm 0.200 in . sp 880 cfm 0.250 in . sp 865 max . inlet temp . 140 degrees f inlet and outlet dia . 11 7 8 in . 60 hz 1 phase motor hp 3 8 motor rpm 3250 motor enclosure totally enclosed speed control mfr . no. 1dgv2 br b features b ul li bearing type ball li li cfm 0.000 in . sp 940 li li cfm 0.125 in . sp 903 li li cfm 0.200 in . sp 880 li li cfm 0.250 in . sp 865 li li cfm 0.375 in . sp 834 li li cfm 0.400 in . sp 819 li li cfm 0.500 in . sp 783 li li cfm 0.600 in . sp 746 li li cfm 0.750 in . sp 689 li li cfm 0.800 in . sp 670 li li cfm 1.000 in . sp 596 li li cfm 1.200 in . sp 505 li li cfm 1.500 in . sp 425 li li cfm duct 940 li li housing dia . in . 16 li li includes mounting bracket li li inlet and outlet dia . in . 11 7 8 li li item inline centrifugal duct fan li li length 8 15 16 li li length in . 10 li li max . amps 3 li li motor hp 3 8 li li motor rpm 3250 li li number of speeds 1 li li phase 1 li li type centrifugal in line li li housing finish baked enamel li li housing material galvanized steel li li hz 60 li li max . wattage 326 li li motor enclosure totally enclosed li li mounting position horizontal or vertical li li speed control mfr . no. 1dgv2 li li voltage 115 li li agency compliance c ul us li li max . inlet temp . deg . f 140 li li standards c ul us li li fits duct dia . in . 12 li li fits duct dia . 12 li li inlet and outlet dia . 11 7 8 li li housing dia . 16 li li green environmental attribute product contributes to reducing energy consumption li li green certification or other recognition energy star rated li li max . inlet temp . 140 degrees f li ul
fantech