joint compound
honeywell ms7510w2008 electric actuator 88 in . lb . 40 to140
actuator spring return shaft type self centering clamping torque in . lbs . 88 stroke deg . 95 3 height in . 9 3 4 width in . 3 15 16 depth in . 2 15 16 switch type modulating floating electrical connections wire cable whip power consumption 14 va timing sec . 90 voltage 24 includes 3 foot cable br b features b ul li ambient temp . range f 40 a 140 li li depth 2 15 16 li li depth in . 2 15 16 li li electrical connections 18 awg color coded cable li li for use with air dampers air handlers ventilation flaps louvers li li height 9 3 4 li li height in . 9 3 4 li li includes 3 ft. cable mounting bracket self centering shaft adapter 3mm crank li li item electric actuator li li stroke deg . 95 3 li li torque in . lbs . 88 li li type spring return li li width 3 15 16 li li width in . 3 15 16 li li ambient temp . range 40 degrees to 140 degrees f li li mounting type direct mount li li power consumption 14va driving 5va holding li li power rating va 14 li li shaft type self centering clamping li li signal type floating li li switch type modulating floating li li voltage 24vac dc li li timing sec . 90 li li spring return spring return li li torque 88 in . lb . li li timing 90 sec . nominal 60 hz 20 sec . spring return li ul
honeywell