thermostats
peco th109 009 multi use thermostat
line voltage ventilation control heating or cooling switch type dpdt control range 40 to 100 f differential 3 f height 7 1 3 in width 3 1 2 in depth 4 7 8 in ambient temp range to 140 f inductive amps 120v 16 208v 13.2 240v 12 contact rating resistive 120 208 240 v 25 bulb size in 1 1 4 diameter coil accuracy 3 degrees f pilot duty rating 125 va standards ul csa nec 547 includes oversized enclosures to accommodate internally mounted relays or terminal blocks br b features b ul li application 2 stage heating or cooling li li color gray li li control range f 40 to 100 li li depth 4 7 8 li li depth in . 4 7 8 li li differential deg . f 3 li li enclosure type rain tight nema 4x 2 piece molded plastic li li features commonly used as a ventilation control in agricultural all exposed metal parts of stainless steel meets national electric code n.e.c. article 547 4 when used with appropriate watertight connections li li for use with agricultural commercial and industrial applications li li full load amps li li full load amps 120v 15a li li full load amps 240vac 12a li li height 7 1 3 li li height in . 7 1 3 li li includes oversized enclosures to accommodate internally mounted relays or terminal blocks li li item line volt mechanical tstat li li locked rotor amps 120v 80a li li locked rotor amps 240v 60a li li number of stages 2 li li number of switches 2 li li pilot duty contacts va 125va li li contact rating resistive 120v a 25 li li contact rating resistive 240v a 25 li li sensing bulb dia . in . 1 1 4 li li type 2 stage heating cooling li li width 3 1 2 li li width in . 3 1 2 li li differential 3 degrees f li li display analog li li inductive amps 120v 16.0 li li inductive amps 240v 12.0 li li input voltage li li mounting location indoor outdoor li li mounting type surface li li sensor type stainless steel fluid filled coil li li switch action open close on rise li li switch type 2 spdt li li voltage range 24 120 to 277vac li li resistive amps 208vac 25a li li agency compliance ul csa nec 547 li li characteristics commonly used as a ventilation control in agricultural all exposed metal parts of stainless steel meets national electric code n.e.c. article 547 4 when used with appropriate watertight connections li li standards ul csa nec 547 li li temp . sensitivity deg . f 3 degrees f li li control range 40 degrees to 100 degrees f li li inductive amps 208v 13.2 li li temp . sensitivity 3 degrees f li li contact rating resistive 120v 25a li li contact rating resistive 240v 25a li li contact rating resistive 277v 20a li li sensing bulb dia . 1 1 4 li ul