threading taps
zoeller n371 evaporative cooling pump3 10hp1 1 2npt
submersible evaporative cooling pump 3 10 hp switch type cord length 20 ft. 115 voltage 9.7 amps dia . 10 3 32 in . discharge npt 1 1 2 in . height 10 1 16 in . max . head 19.25 ft. max . dia . solids 3 8 in . gpm of water 5 ft. of head 43 gpm of water 10 ft. of head 34 gpm of water 15 ft. of head 19 gpm of water 20 ft. of head gpm of water 25 ft. of head gpm of water 30 ft. of head max . temp . 130 degrees f min . sump pit dia . 18 in . base material plastic br b features b ul li base material plastic li li bearing type ball li li cord length ft. 20 li li dia . 10 3 32 li li dia . in . 10 1 16 li li discharge npt in . 1 1 2 li li features li li gpm of water 10 ft. of head 34 li li gpm of water 15 ft. of head 19 li li gpm of water 20 ft. of head li li gpm of water 25 ft. of head li li gpm of water 30 ft. of head li li gpm of water 5 ft. of head 43 li li height 10 1 16 li li height in . 10 1 16 li li housing cast iron li li hp 3 10 li li includes li li item submersible evaporative cooling pump li li max . dia . solids in . 3 8 li li max . head ft. 19.25 li li max . temp . 130 degrees f li li max . temp . f 130 li li mechanical seal sic li li thermal protection yes li li type manual li li cord length 20 ft. li li duty continuous li li impeller material glass filled plastic li li motor type shaded pole li li rpm 1550 li li shaft material ss li li shaft seal silicon carbide li li switch type li li top material cast iron li li voltage 115 li li standards li li min . sump pit dia . in . 18 li li amps 9.7 li li max . dia . solids 3 8 li li min . sump pit dia . 18 li li discharge npt 1 1 2 li li max . head 19.25 ft. li ul
zoeller