circuit breakers
dayton 4b052 exh fan36 inslantwalld d115 230 v
slantwall exhaust fan direct drive propeller dia 36 in 10659 cfm 0.000 in sp volts 115 230 60 hz 1 phase full load amps 7.6 3.8 hp 1 2 motor rpm 850 motor type capacitor start motor enclosure tefc fan rpm 850 bearing type permanently lubricated ball height 42 3 4 in width 40 3 4 in max depth 46 in propeller material galvanized steel number of blades 2 18.3 cfm watt 0.000 in sp includes corrosion resistant shutter with quick release latches br b features b ul li bearing type permanently lubricated ball li li cfm watt 0.000 in . sp 18.3 li li cfm 0.000 in . sp 10659 li li cfm 0.050 in . sp 10000 li li cfm 0.100 in . sp 9343 li li cfm watt 0.100 in . sp 14.6 li li cfm 0.125 in . sp 9006 li li cfm 0.150 in . sp 8651 li li cone dia . in . li li dimension a in . 40 3 4 li li dimension b in . 42 3 4 li li dimension c in . 27 1 8 li li dimension d in . 17 1 4 li li dimension e in . 3 1 4 li li dimension f in . 46 li li dimension g in . li li dimension h in . li li flange width in . 1 21 32 li li for use with li li free area square ft. li li full load amps 7.6 3.8 li li height in . 42 3 4 li li hp 1 2 li li includes corrosion resistant shutter with quick release latches li li item exhaust fan li li motor rpm 850 li li number of blades 2 li li opening required h in . 42 3 4 li li opening required w in . 40 3 4 li li phase 1 li li propeller dia . in . 36 li li shaft dia . in . li li type slant wall direct drive li li venturi clearance dia . in . 36 5 8 li li width in . 40 3 4 li li fan rpm 850 li li hz 60 li li max . ambient temp . f 104 li li mesh size li li motor enclosure totally enclosed fan cooled li li motor type capacitor start li li mounting location wall li li voltage 115 230 li li watts 670 li li cfm watt 0.050 in . sp 16.3 li li cfm watt 0.150 in . sp 12.9 li li frame material galvanized steel li li agency compliance li li propeller material galvanized steel li li requires li li frame finish galvanized steel li li max . depth in . 46 li li motor insulation class b li li cone depth in . li li venturi depth in . 4 1 8 li li cfm 0.040 in . sp li li cfm watt 0.040 in . sp li ul