valves
asco 8210g075 solenoid valve general 2 way nc 1 2 in
gas shutoff valve general service number of ways 2 configuration normally closed cv flow factor 3.60 1 2 pipe size in . 5 8 orifice dia . in . psi differential min . 0 psi differential max . 50 125 max . fluid temp . f voltage 120 60110 50 ac coil insulation class f coil enclosure watertight types 1 2 3 3s 4 and 4x with 1 2 in . conduit hub body material brass gasket material nbr construction reference no. 1 length 3.42 in . width 2.28 in . height 3.95 in . br b features b ul li application for control of commercial and industrial gas burners li li btuh 281000 li li coefficient of volume 3.6 li li construction reference no. 1 li li electrical connections 1 2 conduit with 18 leads li li height 3.95 li li item fuel gas solenoid valve li li length 3.42 li li max . fluid temp . f 125 li li pressure differential max . 50 li li psi differential min . 0 li li orifice dia . in . 5 8 li li pipe size in . 1 2 li li safe working water psi 300 li li steam capacity lb . hr . 193000 li li type general service li li width 2.28 li li ambient temp . range 32 degrees to 125 degrees f li li body material brass li li configuration normally closed li li cv flow factor 3.60 li li gasket material nbr li li hz 50 60 li li nema rating 1 2 3 3s 4 4x li li overall height 3 15 16 li li overall length 3 27 64 li li overall width 2 9 32 li li pipe size 1 2 li li safe working steam psi 300 li li seal material nbr li li voltage 110 120vac li li watts 10.1 li li agency compliance ul fm csa fos safety shutoff li li coil enclosure general purpose no junction box and watertight li li number of ways 2 li li center line pipe center size in . 3.39 li li standards ul fm csa for safety shutoff li li valve design 2 way 2 position li li coil insulation class f li li psi differential max . 50 li li coil key b li li max . fluid temp . 125 degrees f li li orifice dia . 5 8 li li center line pipe center size 4 li li valve configuration normally closed li li max . operating pressure differential 50 psi li li min . operating pressure differential 0 psi li ul