valves
dayton 1a579 solenoid valve 2 way nc 1 in brass
solenoid valve less coil body material brass 2 way normally closed pipe size 1 in . orifice dia . 1 in . coefficient of volume 13.00 min . operating pressure differential 5 psi max . operating pressure differential 125 psi safe working water pressure 250 psi operation type pilot operated flow range 29.1 to 145.5 gpm airflow 286 to 910 scfm gasket material buna n max . fluid temp . 180 degrees f overall length 4 5 32 in . overall height 4 21 32 in . for use with dayton solenoid coils br b features b ul li airflow scfm 910 286 li li coefficient of volume 13.00 li li construction reference no. 2 li li flow range 29.1 to 145.5 gpm li li for use with dayton solenoid coils li li gpm max . 145.5 li li height 4 21 32 li li item solenoid valve less coil li li length 4 5 32 li li max . fluid temp . f 180 li li min . flow rate gpm 29.1 li li pressure differential max . 125 li li psi differential min . 5 li li orifice dia . in . 1 li li pipe size in . 1 li li safe working water psi 250 li li width 2 5 16 li li body material brass li li configuration normally closed li li cv flow factor 13 li li gasket material buna n li li operation type pilot operated li li overall height 4 21 32 li li overall length 4 5 32 li li pipe size 1 li li voltage 24vdc li li agency compliance csa nfpa ul li li coil enclosure nema 1x li li number of ways 2 li li center line pipe center size in . 27 32 li li valve design 2 way li li coil insulation class f li li max . psi differential air water 125 li li max . fluid temp . 180 degrees f li li orifice dia . 1 li li airflow 286 to 910 scfm li li valve configuration normally closed li li max . operating pressure differential 125 psi li li min . operating pressure differential 5 psi li li safe working water pressure 250 psi li ul