water heaters
rheem ruud g100 80n commercial water heater lownox 100g ng naeca
commercial gas water heater tank capacity 100 gal . fuel type natural gas 76000 btuh jacket dia . 28 1 4 in . draft hood size 4 in . height to top of vent connection 69 5 8 in . recovery 90 f rise 82 gph low nox burner yes voltage 120vac first hour recovery 144 gph max . pressure 150 psi temp . range 40 degrees to 160 degrees f vent type standard ignition type standing pilot manual lite energy factor gas connection 1 2 in . top water connection size 1 in . br b features b ul li btuh 76000 li li draft hood size in . 4 li li features space saving design automatic controls li li gas connection in . 1 2 li li gas type natural li li height gas connection in . 15 li li height to t & p opening in . 57 13 16 li li height top of heater in . 65 3 4 li li height top of vent connection in . 69 5 8 li li includes brass drain valve and factory installed t and p valve li li item commercial gas water heater li li jacket dia . in . 28 1 4 li li recovery 100 f rise gph 74 li li tank gal . 100 li li temp . range 40 degrees to 160 degrees f li li temp . range f 40 to 160 li li type lownox li li vent type standard li li energy factor li li fuel type natural gas li li ignition type standing pilot manual lite li li input btu 76000 li li max . pressure psi 150 li li recovery 90 f rise gph 82 li li tank capacity 100 gal . li li top nipple spacing in . 11 li li voltage 120vac li li manufacturers warranty length limited 3 yr . tank and 1 yr . parts li li standards csa meets or exceeds national appliance energy conservation act and ashrae requirements li li recovery 50 f rise gph 147 li li recovery 70 f rise gph 105 li li recovery 110 f rise gph 67 li li recovery 120 f rise gph 61 li li recovery 130 f rise gph 57 li li recovery 140 f rise gph 53 li li max . pressure 150 psi li li top water connection in . 1 li li compliance certified for use in potable water applications in ca and vt li li gas connection 1 2 li li draft hood size 4 li li first hour recovery 144 gph li li jacket dia . 28 1 4 li li recovery 100 f rise 74 gph li li recovery 110 f rise 67 gph li li recovery 120 f rise 61 gph li li recovery 130 f rise 57 gph li li recovery 140 f rise 53 gph li li recovery 50 f rise 147 gph li li recovery 70 f rise 105 gph li li recovery 90 f rise 82 gph li li top nipple spacing 11 li li height to top of vent connection 69 5 8 li li low nox burner yes li li top water connection size 1 li li height to top of heater 65 3 4 li li height to gas connection 15 li ul