thermostats
johnson controls a19abc 37c thermostat 2 spdt range 30 to 100
line voltage thermostat heating cooling switch type 2 spdt switch action open close on rise number of switches 1 overall length 4 3 8 in . sensor type bulb for use with hvac r applications color gray application heating and cooling enclosure type galvanized steel 120 to 277 120 to 277 16 16 9.2 8 16 8 96 48 16 8 96 48 16 22 22 22 22 125 flat surface 1 1 1 no ul e6688 ; csa lr948 4813 02 br b features b ul li application heating and cooling li li capillary length in . 120 li li color gray li li control range f 30 to100 degrees f li li depth 1 13 16 li li depth in . 1 13 16 li li differential deg . f 6 to 24 li li enclosure type galvanized steel li li for use with hvac r applications li li full load amps 16a li li full load amps 120v 16a li li full load amps 240vac 8a li li height 4 3 8 li li height in . 4 3 8 li li item line volt mechanical tstat li li locked rotor amps 120v 96a li li locked rotor amps 240v 48a li li number of relay inputs 1 li li number of relay outputs 1 li li number of stages 1 li li number of switches 1 li li pilot duty contacts va 125va li li contact rating resistive 120v a 22 li li contact rating resistive 240v a 22 li li sensing bulb dia . in . 3 8 li li sensing bulb length in . 4 li li switch ratings 120vdc a 16 li li type heating cooling li li width 2 1 8 li li width in . 2 1 8 li li 0 10v output no li li differential 6 degrees to 24 degrees f li li inductive amps 120v 16a li li inductive amps 240v 8a li li input voltage 120 to 277vac li li mounting flat surface li li mounting type flat surface li li overall length 4 3 8 li li contact rating resistive 277v a 22 li li sensor type bulb li li switch action open close on rise li li switch type spdt li li fan switching no li li system switching yes li li voltage range 120 to 277vac li li cooling full load 120v 16a li li cooling locked rotor 120v 96a li li cooling locked rotor 240v 48a li li cooling full load 240v 8a li li resistive amps 208vac 22a li li agency compliance ul e6688 ; csa lr948 4813 02 li li standards ul e6688 ; csa lr948 4813 02 li li temp . sensitivity deg . f 2 1 2 li li control range 30 degrees to100 degrees f li li inductive amps 208v 9.2 a li li capillary length 120 li li temp . sensitivity 2 degrees f li li contact rating resistive 120v 22a li li contact rating resistive 240v 22a li li switch ratings 120vdc 16a li li contact rating resistive 277v 22a li li sensing bulb dia . 3 8 li li sensing bulb length 4 li ul