plumbing pumps
dayton 1xhv6 submersible sump pump 1 3 hp 4.1 amps
submersible sump pump 1 3 hp switch type none cord length 10 ft. 115 voltage 3.8 amps dia . 7 1 2 in . discharge npt 1 1 2 in . height 13 3 4 in . max . head 31 ft. max . dia . solids 1 4 in . gpm of water 5 ft. of head 58 gpm of water 10 ft. of head 46 gpm of water 15 ft. of head 31 gpm of water 20 ft. of head 19 gpm of water 25 ft. of head 9 gpm of water 30 ft. of head 2 max . temp . 104 degrees f min . sump pit dia . 8 in . base material cast iron housing aluminum br b features b ul li base material cast iron li li bearing type ball li li cord length ft. 10 li li dia . 7 1 2 li li dia . in . 7 1 2 li li discharge npt in . 1 1 2 li li gpm of water 10 ft. of head 46 li li gpm of water 15 ft. of head 31 li li gpm of water 20 ft. of head 19 li li gpm of water 25 ft. of head 9 li li gpm of water 30 ft. of head 2 li li gpm of water 5 ft. of head 58 li li height 13 3 4 li li height in . 13 3 4 li li housing aluminum li li hp 1 3 li li item submersible sump pump li li max . dia . solids in . 1 8 li li max . head ft. 31 li li max . temp . 104 degrees f li li max . temp . f 104 li li mechanical seal crb cmc li li thermal protection yes li li type manual li li cord length 10 ft. li li duty continuous li li impeller material ep li li motor type psc li li rpm 3450 li li shaft material ss li li shaft seal 2 carbon ceramic 1 buna n li li switch type none li li top material cast aluminum li li voltage 115 li li standards csa li li min . sump pit dia . in . 8 li li amps 3.8 li li max . dia . solids 1 4 li li min . sump pit dia . 8 li li discharge npt 1 1 2 li li max . head 31 ft. li ul