water heaters
rheem ruud g100 200 water heater 100 gal . 199900 btuh
commercial gas water heater tank capacity 100 gal . fuel type lp 199900 btuh jacket dia . 30 1 4 in . draft hood size 6 in . height to top of vent connection 73 1 16 in . recovery 90 f rise 215 gph low nox burner no voltage 120vac first hour recovery 264 gph max . pressure 150 psi temp . range 100 degrees to 180 degrees f vent type standard ignition type spark to pilot energy factor gas connection 3 4 in . top water connection size 1 1 2 in . height to top of heater 66 1 8 in . br b features b ul li btuh 199900 li li draft hood size in . 6 li li features universal tank space saver design spark to pilot ignition system sentinel led diagnostic system li li gas connection in . 3 4 li li gas type liquid propane li li height cold side connection in . 23 1 4 li li height gas connection in . 7 li li height side hot connection in . 57 1 2 li li height to t & p opening in . 57 1 2 li li height top of heater in . 66 1 8 li li height top of vent connection in . 73 1 16 li li includes automatic flue damper full port full flow brass drain valve li li item commercial gas water heater li li jacket dia . in . 30 1 4 li li recovery 100 f rise gph 194 li li tank gal . 100 li li temp . range 100 degrees to 180 degrees f li li temp . range f 100 to 180 li li type gas li li vent type standard li li energy factor li li fuel type lp li li ignition type spark to pilot li li input btu 199900 li li max . pressure psi 150 li li recovery 90 f rise gph 215 li li tank capacity 100 gal . li li top nipple spacing in . 23 li li voltage 120vac li li manufacturers warranty length limited 3 yr . tank and 1 yr . parts li li standards tested according to ansi standards exceed thermal efficiency and standby loss requirements of ashrae exceeds energy efficiency codes including ca energy commission li li recovery 50 f rise gph 388 li li recovery 70 f rise gph 277 li li recovery 110 f rise gph 176 li li recovery 120 f rise gph 162 li li recovery 130 f rise gph 149 li li recovery 140 f rise gph 138 li li max . pressure 150 psi li li top water connection in . 1 1 2 li li side water connection in . 2 li li first hour recovery gph 264 li li compliance certified for use in potable water applications in ca and vt li li gas connection 3 4 li li draft hood size 6 li li first hour recovery 264 gph li li jacket dia . 30 1 4 li li recovery 100 f rise 194 gph li li recovery 110 f rise 176 gph li li recovery 120 f rise 162 gph li li recovery 130 f rise 149 gph li li recovery 140 f rise 138 gph li li recovery 50 f rise 388 gph li li recovery 70 f rise 277 gph li li recovery 90 f rise 215 gph li li top nipple spacing 23 li li height to top of vent connection 73 1 16 li li low nox burner no li li top water connection size 1 1 2 li li height to top of heater 66 1 8 li li height to cold side connection 23 1 4 li li height to hot side connection 57 1 2 li li height to gas connection 7 li li side water connection size 2 li ul