water heaters
rheem ruud es120 24 g commercial water heater 120 gal . 480vac
electric water heater commercial tank capacity 120 gal . voltage 480vac 1 or 3 phase 24000 total watts overall height 67 5 8 in . jacket dia . 30 1 4 in . overall width 36 in . recovery 90 f rise 110 gph recovery 50 f rise 199 gph recovery 70 f rise 142 gph recovery 100 f rise 99 gph recovery 110 f rise 90 gph recovery 120 f rise 83 gph recovery 130 f rise 76 gph recovery 140 f rise 71 gph height to cold side connection 4 3 4 in . br b features b ul li amps ac 50 for 1 phase 29 for 3 phase li li features inputs of 3kw to 108kw four voltages to choose from lifeguard stainless steel elements 98 % thermal effeciency system sentenal full port full flow brass drain valve li li height to t & p opening in . 67 5 8 li li height top of heater in . 67 5 8 li li includes t and p valve full port full flow brass drain valve system sentinal li li item electric water heater li li jacket dia . in . 30 1 4 li li number of elements 6 li li phase 1 or 3 li li recovery 100 f rise gph 99 li li tank gal . 120 li li temp . range 120 degrees to 180 degrees f li li temp . range f 120 degrees to 180 degrees li li type electric li li connection location side li li max . pressure psi 150 li li overall height 67 5 8 li li overall width 36 li li recovery 90 f rise gph 110 li li tank capacity 120 gal . li li total watts 24000 li li voltage 480vac li li manufacturers warranty length 3 yr . limited tank 1 yr . limited parts li li standards ul certified li li water connection 1 1 2 npt li li recovery 50 f rise gph 199 li li recovery 70 f rise gph 142 li li recovery 110 f rise gph 90 li li recovery 120 f rise gph 83 li li recovery 130 f rise gph 76 li li recovery 140 f rise gph 71 li li max . pressure 150 psi li li top water connection in . 1 1 2 li li compliance tested according to doe test procedures and exceed the minimum energy factor requirements of current ashrae standards exceeds energy effeciency codes of all states . design certified by underwriters laboratory ul to meet ul standard 1453 and ul nsf005 . li li green environmental attribute not applicable li li jacket dia . 30 1 4 li li recovery 100 f rise 99 gph li li recovery 110 f rise 90 gph li li recovery 120 f rise 83 gph li li recovery 130 f rise 76 gph li li recovery 140 f rise 71 gph li li recovery 50 f rise 199 gph li li recovery 70 f rise 142 gph li li recovery 90 f rise 110 gph li li height to cold side connection 4 3 4 li li height to hot side connection 67 5 8 li li residential commercial commercial li ul