ducting
fantech hp 190sl radon fanfirst duct dia 4 1 2in 115v
radon fan in line fits duct dia . 4 1 2 in . max . static pressure 2.15 in . voltage 115 inlet and outlet dia . 4 1 2 in . cfm 0.000 in . sp 158 cfm 0.500 in . sp 133 cfm 0.750 in . sp 117 cfm 1.000 in . sp 103 cfm 1.500 in . sp 76 maximum inlet temp . 140 degrees f hz 60 max . amps 0.78 1 phase max . wattage 88 bearing type sealed ball height 17 3 4 in . depth 7 3 16 in . flange width 3 4 in . housing material uv resistant polycarbonate mounting position vertical br b features b ul li max . static pressure 2.15 li li type in line li li bearing type sealed ball li li cfm 0.750 in . sp 117 li li includes integral condensate bypass li li fits duct dia . 4 1 2 li li cfm 1.500 in . sp 76 li li depth 7 3 16 li li flange width 3 4 li li cfm 1.000 in . sp 103 li li phase 1 li li warranty 5 years li li housing material uv resistant poycarbonate li li hz 60 li li voltage 115 li li inlet and outlet dia . 4 1 2 li li cfm 0.000 in . sp 158 li li max . amps 0.78 li li cfm 0.500 in . sp 133 li li maximum inlet temp . 140 deg f li li max . wattage 85 li li agency compliance culus for wet locations li li item radon fan li li height 17 3 4 li li mounting position vertical li ul
fantech