water heaters
rheem ruud he119 199 comm water heater 119g ng naeca
commercial high efficiency gas water heater tank capacity 119 gal . fuel type natural gas 199000 btuh jacket dia . 27 in . draft hood size 3 in . height to top of vent connection intake 22 in . exhaust 9 1 2 in . recovery 90 f rise 255 gph low nox burner yes voltage 120vac first hour recovery 312gph max . pressure 150 psi temp . range 70 degrees to 160 degrees f vent type power direct vent ignition type spark to pilot energy factor gas connection 3 4 to 1 2 in . br b features b ul li btuh 199000 li li draft hood size in . 3 li li features integrated self diagnostic system control thermostat gas valve and electronic ignition system li li gas connection in . 3 4 to 1 2 li li gas type natural li li height cold side connection in . 6 3 4 li li height gas connection in . 28 7 8 li li height side hot connection in . 66 3 4 li li height to t & p opening in . 66 3 4 li li height top of heater in . 73 li li height top of vent connection in . intake 22 exhaust 9 1 2 li li includes t and p valve li li item commercial high efficiency gas water heater li li jacket dia . in . 27 li li recovery 100 f rise gph 229 li li tank gal . 119 li li temp . range 70 degrees to 160 degrees f li li temp . range f 70 to 160 li li type commercial li li vent type power direct vent li li energy factor li li fuel type natural gas li li ignition type spark to pilot li li input btu 199000 li li max . pressure psi 150 li li recovery 90 f rise gph 255 li li tank capacity 119 gal . li li voltage 120vac li li manufacturers warranty length limited 3 yr . tank and 1 yr . parts li li standards meets or exceeds national appliance energy conservation act and ashrae requirements li li recovery 50 f rise gph 458 li li recovery 70 f rise gph 327 li li recovery 110 f rise gph 208 li li recovery 120 f rise gph 191 li li max . pressure 150 psi li li side water connection in . 1 1 2 li li compliance certified for use in potable water applications in ca and vt li li green environmental attribute commercial gas heater has thermal efficiency rating 0.90 li li gas connection 3 4 to 1 2 li li draft hood size 3 li li first hour recovery 312gph li li jacket dia . 27 li li recovery 100 f rise 229 gph li li recovery 110 f rise 208 gph li li recovery 120 f rise 191 gph li li recovery 50 f rise 458 gph li li recovery 70 f rise 327 gph li li recovery 90 f rise 255 gph li li height to top of vent connection intake 22 exhaust 9 1 2 li li low nox burner yes li li top water connection size 1 1 2 li li height to top of heater 73 li li height to cold side connection 6 3 4 li li height to hot side connection 66 3 4 li li height to gas connection 28 7 8 li li side water connection size 1 1 2 li ul