valves
red hat 8262h021v solenoid valve oil shutoff 2 way nc
solenoid valve oil shutoff number of ways 2 configuration normally closed cv flow factor 0.21 1 4 pipe size in . 3 32 orifice dia . in . psi differential min . 0 psi differential max . 500 safe working water psi 300 180 max . fluid temp . f voltage 110 120vac coil insulation class f coil enclosure watertight types 1 2 3 3s 4 and 4x with 1 2 in . conduit hub body material brass gasket material fkm construction reference no. 2 length 1.56 in . width 1.69 in . height 2.85 in . br b features b ul li application for control of commercial and industrial oil burners li li coefficient of volume 0.21 li li construction reference no. 2 li li electrical connections 1 2 conduit li li height 2.85 li li item fuel oil solenoid valve li li length 1.56 li li max . fluid temp . f 180 li li max . operating pressure differential light oil 270 li li max . operating pressure differential air inert gas 500 li li pressure differential max . 500 li li psi differential min . 0 li li max . operating pressure differential water 350 li li orifice dia . in . 3 32 li li pipe size in . 1 4 li li safe working water psi 300 li li type oil shutoff li li width 1.69 li li ambient temp . range 5 degrees to 131 degrees f li li body material brass li li configuration normally closed li li cv flow factor 0.21 li li gasket material fkm li li hz 50 60 li li nema rating 1 2 3 3s 4 4x li li overall height 2 27 32 li li overall length 1 9 16 li li overall width 1 11 16 li li pipe size 1 4 li li seal material fkm li li voltage 110 120vac li li watts 9.1 li li agency compliance ul fm and csa for safety shutoff valve li li coil enclosure general purpose no junction box and watertight li li number of ways 2 li li center line pipe center size in . 2.6 li li standards ul fm csa for safety shutoff li li valve design 2 way 2 position li li coil insulation class f li li psi differential max . 500 li li max . psi differential air water 350 li li max . fluid temp . 210 degrees f li li orifice dia . 3 32 li li center line pipe center size 2 19 32 li li valve configuration normally closed li li max . operating pressure differential 350 psi li li min . operating pressure differential 0 psi li ul