hammers
dayton5pv26hydronic unit heaternpt 3 818 1 2h20 1 2w10 1 2d
hydronic unit heater heater type water only fan guard type osha output 200 f water 35900 btuh air flow 850 cfm motor hp 1 20 1.4 amps inlet outlet npt 3 8 in . height 18 1 2 in . width 20 1 2 in . depth 10 1 2 in . air flow direction horizontal coil type serpentine voltage 115 60 hz 1 phase max . operating psi 75 max . operating temp . 320 degrees f motor enclosure totally enclosed mounting height 9 ft. standards etl certified br b features b ul li cfm 850 li li depth 10 1 2 li li depth in . 10 1 2 li li height 18 1 2 li li height in . 18 1 2 li li item hydronic unit heater li li max . operating psi 75 li li motor hp 1 20 li li mounting height ft. 9 li li output 200 f water btuh 35900 li li phase 1 li li pipe size in . 3 8 li li type water only li li width 20 1 2 li li width in . 20 1 2 li li air flow 850 cfm li li coil type serpentine li li hz 60 li li max . operating temp . 320 degrees f li li motor enclosure totally enclosed li li supply and return connection 3 8 copper li li voltage 115 li li fan guard type osha li li agency compliance etl certified li li heater type water only li li max . operating temp . f 320 li li standards etl certified li li requires 1 2 i.d. fitting for connection li li amps 1.4 li li air flow direction horizontal li li mounting height 9 ft. li li inlet outlet npt 3 8 li li output 200 f water 35900 btuh li ul