water heaters
rheem ruud e10 18 g commercial water heater 10 gal . 240vac
electric water heater commercial tank capacity 10 gal . voltage 240vac 3 phase 18000 total watts overall height 23 in . overall length 21 1 2 in . overall width 21 3 4 in . recovery 90 f rise 82 gph recovery 50 f rise 147 gph recovery 70 f rise 105 gph recovery 100 f rise 74 gph recovery 110 f rise 67 gph recovery 120 f rise 61 gph recovery 130 f rise 57 gph recovery 140 f rise 53 gph height to cold side connection 11 3 4 in . br b features b ul li amps ac 43 li li front to back of heater in . 21 3 4 li li height cold side connection in . 11 3 4 li li height side hot connection in . 19 3 4 li li height to t & p opening in . 15 3 4 li li height top of heater in . 23 li li includes t and p valve full port drain valve and 6 stainless steel legs li li item electric water heater li li number of elements 3 li li phase 3 li li recovery 100 f rise gph 74 li li tank gal . 10 li li temp . range 90 degrees to 190 degrees f li li type commercial li li width in . 21 1 2 li li connection location side li li overall height 23 li li overall length 21 1 2 li li overall width 21 3 4 li li recovery 90 f rise gph 82 li li tank capacity 10 gal . li li total watts 18000 li li voltage 240vac li li manufacturers warranty length 3 yr . limited tank 1 yr . limited parts li li standards national sanitation foundation and federal state county and local department sanitation codes li li water connection 1 1 4 npt li li recovery 50 f rise gph 147 li li recovery 70 f rise gph 105 li li recovery 110 f rise gph 67 li li recovery 120 f rise gph 61 li li recovery 130 f rise gph 57 li li recovery 140 f rise gph 53 li li max . pressure 150 psi li li compliance certified for use in potable water applications in ca and vt li li recovery 100 f rise 74 gph li li recovery 110 f rise 67 gph li li recovery 120 f rise 61 gph li li recovery 130 f rise 57 gph li li recovery 140 f rise 53 gph li li recovery 50 f rise 147 gph li li recovery 70 f rise 105 gph li li recovery 90 f rise 82 gph li li height to cold side connection 11 3 4 li li height to hot side connection 19 3 4 li li residential commercial commercial li ul