pipe fittings & couplers
maxitrol 325 7al 1010 0006 line pressure regulator1 1 4 in fnpt
gas pressure regulator regulator type lever acting line pipe size 1 1 4 in . mounting position multipoise capacity 1250000 btuh max . inlet pressure 2 psi venting 1 1 4 in . npt max . load 1250000 btuh gas type lp or ng connection type fnpt outlet pressure range 7 to 11 in . wc ambient temp . range 40 degrees to 205 degrees f inlet emergency exposure limits 65 psi 200 cu . ft. hr . 0.3 in . wc pressure drop standards csa design certified z21 .80 can 6.22 br b features b ul li pipe size 1 1 4 li li venting 1 1 4 li li ambient temp . limits f 40 to 205 li li cu . ft. hr . 0.3 in . wc pressure drop 200 li li cu . ft. hr . 2.0 in . wc pressure drop 460 li li cu . ft. hr . 7.0 in . wc pressure drop 900 li li cu . ft. hr . 3.0 in . wc pressure drop 565 li li type lever acting li li max . inlet pressure psi 2 li li cu . ft. hr . 3 4 psi pressure drop 1480 li li max . load 1250000 btu hr li li outlet pressure range in . wc 7 to 11 li li cu . ft. hr . 1 psi pressure drop 1710 li li item line pressure regulator li li inlet emergency exposure limits psi 65 li li connection fnpt li li cu . ft. hr . 1.0 in . wc pressure drop 325 li li mounting position multipoise li li cu . ft. hr . 4.0 in . wc pressure drop 650 li li capacity 1250000 btu hr li li cu . ft. hr . 1 2 psi pressure drop 1210 li ul