plumbing pumps
goulds water technology ws7534d4 sewage pump 7 1 2 hp 3ph 460v
submersible sewage pump manual 7 1 2 hp base material cast iron housing cast iron impeller material cast iron voltage 460 phase 3 amps 11.5 height 28 1 4 in . cord length 20 ft. discharge size 4 in . npt max . dia . solids 3 in . max . head 60 ft. max . temp . 104 degrees f thermal protection no bearing type ball br b features b ul li base material cast iron li li bearing type ball li li cord length ft. 20 li li dia . 15 3 4 li li dia . in . 15 3 4 li li discharge npt in . 4 ansi flange li li gpm of water 20 ft. of head 620 li li gpm of water 25 ft. of head 490 li li gpm of water 30 ft. of head 330 li li gpm of water 40 ft. of head 150 li li gpm of water 50 ft. of head 155 li li height 28 1 4 li li height in . 28 1 4 li li housing cast iron li li hp 7 1 2 li li item submersible sewage pump li li max . dia . solids in . 3 li li max . head ft. 60 li li max . temp . 104 degrees f li li max . temp . f 104 li li off point in . n a li li on point in . n a li li phase 3 li li thermal protection no li li type manual li li cord length 20 ft. li li impeller material cast iron li li motor type 3 phase li li pump type manual li li rpm 1750 li li shaft material stainless steel li li shaft seal silicon carbide li li top material cast iron li li voltage 460 li li standards ul listed csa certified li li amps 11.5 li li max . dia . solids 3 li li max . head 60 ft. li li off point n a li li discharge size 4 npt li ul