insulation
morris products 96114 above ground insulation piercing connectors main 4 0 2 tap 4 0 4
above ground insulation piercing connectors main 40 2 tap 40 4 anyone can use our diy above ground connector features diy connector installs in just minutes saving many man hours on the job eliminates wire stripping connecting taping of split bolts and adding inhibitor above ground connector can be installed on energized circuits eliminating power shutdowns overhead services both insulated bare mains above grade urd services street lighting non tension splicing tapping insulated replacement for split bolts tapping without cutting the main gutter taps double shear head bolt guarantees correct torque tightening every time ensuring a quality connection eliminating the possibility of hot spots damaged wires or loose connections no cable stripping required simply insert the jacketed cable into the entry port tighten with a 12 6 point socket turbo spacer allows tap side to remain open while you hand tighten the diy above ground connector on the main wire all models except 96102 96104 blue rubber insert recreates insulation when used on bare wire used to avoid any damage on neutral messenger only on models 96106 96110 96112 96114 the bolt and all external parts of the connector are completely isolated from energized parts and the bolt is covered by the plastic shear head the installer has no contact at any point with an energized part can be installed on energized conductors however the tap must not be under load corrosion free connection is good for hot cold damp salty connections properly installed the connector seals water tight this is accomplished by a sealant tank that during installation is compressed and forces sealant out to protect the connection from oxygen and water copper teeth are tin plated shell is high strength uv resistant thermoplastic insulating material steel bolts are galvanized the connector bodies are made from high strength fiber reinforced thermoplastic and galvanized steel bolts ul486b listed for cu to cu al to al cu to al ; 600 volt 194f 90c rated meets ansi c119 4 requirements specification number of ports 1 torqueinch lb 160 bolt head size 12 in main range 40 2 tap range 40 4 dimension height 4 3 in x width 2 4 in x length 3 2 in item weight 0 43 lbs sku mspr318
morris products