water transfer pumps
dayton 3bb75 pump sump 3 4 hp
submersible sump pump 3 4 hp switch type none cord length 15 ft. 115 voltage 10.5 amps dia . 10 in . discharge npt 1 1 2 in . height 13 in . max . head 37 ft. max . dia . solids 1 2 in . gpm of water 5 ft. of head 113 gpm of water 10 ft. of head 101 gpm of water 15 ft. of head 92 gpm of water 20 ft. of head 80 gpm of water 25 ft. of head 63 gpm of water 30 ft. of head 43 max . temp . 104 degrees f base material cast iron housing cast iron top material cast iron br b features b ul li base material cast iron li li bearing type upper and lower li li cord length ft. 15 li li dia . 10 li li dia . in . 10 li li discharge npt in . 1 1 2 li li features li li gpm of water 10 ft. of head 101 li li gpm of water 15 ft. of head 92 li li gpm of water 20 ft. of head 80 li li gpm of water 25 ft. of head 63 li li gpm of water 30 ft. of head 43 li li gpm of water 5 ft. of head 113 li li height 13 li li height in . 13 li li housing cast iron li li hp 3 4 li li includes li li item submersible sump pump li li max . dia . solids in . 1 2 li li max . head ft. 37 li li max . temp . 104 degrees f li li max . temp . f 104 li li mechanical seal sic li li thermal protection li li type manual li li cord length 15 ft. li li duty continuous li li impeller material cast iron li li motor type oil cooled li li rpm li li shaft material stainless steel li li shaft seal silicon carbide li li switch type none li li top material cast iron li li voltage 115 li li standards li li amps 10.5 li li max . dia . solids 1 2 li li discharge npt 1 1 2 li li max . head 37 ft. li ul