circuit breakers
square d qo403l60nrb load center
load center main circuit breaker or main lug main lug fixed amps 60 number of spaces 3 max . no . of tandem breakers 0 recommended surface cover included height 13 1 4 in . width 7 in . depth 4 in . circuit breaker type qo voltage 208y 120vac 240 120v delta ac or 240v delta ac short circuit current rating 65ka phase 3 bus material shielded tin plated copper enclosure nema rating 3r recommended ground bar kit 5b718 br b features b ul li copper awg kcmil 10 to 6 li li depth 4 li li depth in . 4.12 li li height 13 1 4 li li height in . 13.18 li li item load center li li max . no . of 1 pole breakers 3 li li max . no . of tandem breakers 0 li li number of spaces 3 li li phase 3 li li type main lugs li li width 7 li li width in . 6.92 li li bus material shielded tin plated copper li li enclosure outdoor li li ground bar kit g1124365 li li nema rating 3r li li surface cover included li li voltage 208y 120vac 240 120v delta ac or 240v delta ac li li circuit breaker type qo li li bus shielded one piece li li mains fixed lug li li rms symmetrical amp rating 65000 li li federal specification w p 115c as type 1 class 2 li li standards ul listed rohs compliant federal specification w p 115c as type 1 class 2 li li amps 60 li li short circuit current rating 65ka li li recommended surface cover included li li main circuit breaker or main lug main lug fixed li li enclosure nema rating 3r li li recommended ground bar kit 5b718 li ul
square d