tripp lite smart1500 smart 1500va line-interactive ups 6 outlets
tripp lite s smart1500 tower ups system protect against data loss and downtime tripp lite s smart1500 tower ups system protects connected equipment against data loss downtime and equipment damage due to power outages voltage fluctuations and transient surges . featuring advanced automatic voltage regulation it provides regulated 120v nominal output without using battery power during brownouts and over-voltages . large internal batteries support connected equipment during blackouts . features 6 outlets including one individually controllable outlet that can be used to reboot the smart1500 has 6 outlets including one individually controllable outlet that can be used to reboot select equipment on demand or maximize battery runtime for mission-critical equipment . usb db9 communication ports support messaging of detailed ups operational parameters and line power status . included poweralert ups monitoring and unattended shutdown software provides management support for an unlimited number of network ups systems . the smart1500 comes with 250 000 ultimate lifetime insurance coverage for connected equipment insurance usa canada only and a 2-year product warranty . ideal for protection of service storage devices telecom systems and more the smart1500 provides advanced automatic voltage regulation reliable battery backup and comprehensive power management capability in a compact tower form factor . featuring 6 outlets and usb db9 communication ports the smart1500 offers a complete power protection solution for protection for servers storage devices and telecom equipment . reliable battery backup various electrical and radio sources can cause disruptive interference on the ac line . this line noise is a common cause of incremental hardware damage data corruption and audio video performance problems . the ht10dbs incorporates exclusive isobar technology including isolated filter banks to eliminate interference between connected components plus full emi rfi line noise filtering to ensure peak audio and video performance . powerful ac line surge suppression ups battery backup support enables you to work through short power failures and provides time to save files and perform an orderly system shutdown in case of a prolonged blackout . the smart1500 features a large internal battery that provides 7 min . of battery support for a full load 980 watts and 20 min . for a half-load 490 watts . during normal operation incoming utility power keeps the ups battery fully charged so that backup power will always be available if needed . advanced automatic voltage regulation avr advanced avr protects connected equipment from incremental hardware damage data loss and performance problems that can be caused by low-voltage conditions commonly known as brownouts and overvoltages . the smart1500 corrects brownouts as low as from 75v and overvoltages as high as 147v to a nominal 120v providing safe computer-grade power to all connected components without consuming battery power needed to support equipment through blackouts . surge suppression a sudden power surge or spike can damage or destroy electronic components and wipe out irreplaceable data . the smart1500 features a 480-joule surge suppression rating to protect all connected components and the data they contain . corrects brownouts and protects equipment from blackouts emi rfi line noise filtering various electrical and radio sources can cause disruptive interference on the ac line . this line noise is a common cause of incremental hardware damage data corruption and audio video performance problems . the smart1500 incorporates technology that filters out disruptive line noise preventing it from affecting your equipment . usb db9 ports and included poweralert software the smart1500 features a usb port and a db9 port cables included . used with tripp lite s included poweralert software these communication ports provide comprehensive network power monitoring and control . capabilities include ups and line power status messaging on battery low-battery power restored ac line voltage dc battery voltage and remaining battery capacity timed inverter shutoff after unattended shutdown and ups output power control for delayed or immediate reboot of connected devices . environmentally responsible the smart1500 s efficient design conserves electricity saves money and reduces co2 emissions . this ups system is manufactured in compliance with strict rohs reduction of hazardous substances guidelines to minimize the use of hazardous materials and its replaceable internal battery is 100 recyclable . ultimate peace of mind the smart1500 comes with 250 000 ultimate lifetime insurance coverage for connected equipment insurance usa canada only and a 2-year product warranty . technical specifications voltage compatibility 120 vac frequency compatibility 60 hz va wattage capacity 1500 980 battery runtimes half full 20 min . 7 min . outlet quantity type 6 x 5-15r 1 in individually controllable load bank communications ports 1 x hid-compliant usb 1 x db9 input cord 6 ft. input plug 5-15p right-angle switches leds alarms on off switch alarm cancel self-test switch 5 leds audible alarm dimensions hwd 12.8 x 17.5 x 95 inches weight 38.4 lbs . material of construction plastic agency approvals ul 1778 us csa canada nom mexico fcc part 15 category b emi rohs